For over 20 years, Angier, NC has known that Comfort First is the company to call for expert heating and cooling.
Our Angier, NC reviews show how we hold your heating, cooling and home comfort above all else! Come take a look!
for Angier, NC
Our Reviews by City
Doug - Angier, NC
Carrier split heat pump. Diagnosed leaking evaporator coil
Complete 1 System Trane HP Split System. Performed Heating Maintenance Checked thermostat and air filter. Checked amp draws on heat strips and blower motor. Inspected evap coil. Made sure drain line was clear. Checked all wiring. Checked compressor and cfm amp draws. Tested defrost board. Checked dual cap. Checked pressures. Checked all wiring at condenser. Cleaned condenser coil. System is running great at this time.
Complete: Worked on DS Rheem HP: Replaced 15’ of 16” return duct. Attached to plenum and added collar to connect two pieces of duct. Also noticed band holding return side of system had broken causing unit to not be level. Strapped it back up as well as duct. Cleaned out condensate Ptrap and blew out line. Outside dug down to condensate drain coming out of foundation wall and added an elbow and piped down grade to allow better drainage. Everything looks good and working great at this time.
HP Split System: Checked Air Filters and thermostat. Checked amp draws in blower motor, inspected evap coil. Made sure drain line was clear. Checked all wiring at AH. Checked amp draws in compressor and CFM, checked dual cap. Checked pressures. Checked reversing valve. Cleaned condenser. Tested defrost board. Checked all wiring at condenser. System is running great at this time
Complete one system, split heat pump, two zones. Found blown 5 amp fuse in air handler and replaced it. System is operating properly at this time.
Goodman split heat pump maintenance
Complete 1 system, Trane heat pump split system. Found condenser coil dirty, cleaned it. Added 3 lbs of R22 and a can of leak stop. System is operating properly at this time.
Goodman equipment......cooling tune up
Complete: EPA Maintenance: Goodman Package Unit: Checked Thermostat, Filters and Amp Draws on the Blower Motor, Inspected Evap coil. Checked condensate line. And washed Coils. Checked the charge, and the capacitor. Check the Amp draws on the fan and compressor. Cleaned Unit. System looks good and running Great at this time.
Carrier split heatpump replaced warranty compressor
Goodman split heat pump. Sealed blower doors
Goodman split heat pump cooling maintenance
Trane split heat pump cooling maintenance
Amana split heat pump cooling maintenance
Epa maintenance on 1 amana heatpump split system and 1 goodman split system heatpump.
Rheem heat pump found capacitor bad replaced added hard start to lower amp draw on start up
EPA maintenance on an Amana heat pump system
EPA maintenance on a Trane heat pump system
Rheem heat pump package unit heating maintenance
York Heat Pump
Carrier Heat Pump.
Trane Heat Furnace
Removed nest camera