For over 20 years, Apex, NC has known that Comfort First is the company to call for expert heating and air conditioning repair services.
Our Apex, NC reviews show how we hold your heating, cooling and home comfort above all else! See what your neighbors are saying about our HVAC services below.
for Apex, NC
Our Reviews by City
Jessica - Apex, NC
Donald - Apex, NC
Bradley McLeod was knowledgeable and explained what was wrong with my furnace. He was friendly and pleasant to work with
Professional service, straight shooter.
Matt - Apex, NC
He was great at explaining everything, answered all my questions.
Great service! Professional Representative
Joseph - Apex, NC
I’m extremely pleased with the professional service and maintenance provided by BJ McLeod. Excellent communication and efficient service provided. Everything was checked and serviced in the A/C unit. I’m glad that I now have a Preventative Maintenance Agreement with First Comfort. Thank you very much!
Excellent work Cody and Dennis
Brian - Apex, NC
Fantastic job - quick and efficient, careful and kind. Gave me good info on how to use systems properly. Very professional.
Randy - Apex, NC
Cody and partner were very great. Explained my options and even offered maintenance. Upstairs is cool, wife is cool so all good!
Kristin - Apex, NC
Great job. Done quickly.
Excellent visit. A thorough review of the system.
Wendy - Apex, NC
Nabela - Apex, NC
Inspected duct work
Replaced blower motor on a carrier gas furnace
90 percent furnace drain clogged
Trane gas pack bad gas valve
Temp Star bad blower motor
Lennox gas furnace replaced board
Goodman gas furnace replaced inducer motor
Goodman gas furnace replaced pressure switch and inducer motor
Goodman gas furnace replaced inducer motor and pressure switch
Replaced a furnace control board on a Goodman furnace
Replaced pressure switch on a Trane gas furnace
Goodman furnace found bad gas valve and flame sensor
Replaced pressure switch on a Trane package system
No one home
Goodman gas pack replaced igniter
Amana gas pack bad inducer motor
CARRIER A/C found low voltage wire broke and fuses missing from disconnect
CARRIER gas furnace bad pressure switch and blower motor
Trane gas furnace bad pressure switch
CARRIER heat pump found broke wire going to heat strips
Incomplete: 1 System: 2 Zone Lennox Split HP: HO said that the system wasn’t heating but blowing out air. At the HP found refrigerant levels to be exactly where they need to be for a 410 system and amp draws and all doing what they should be doing. It’s 33 degrees outside and HP is working as it should. Emergency heat US is on but it’s only a 5kw Heat Kit. This system is a 2T system in a 2k sqft home. HO said that several neighbors had expressed similar issues with undersized systems. HO would like an estimate for either and upgrade or if a larger Heat Kit would make a difference. He does have vivant tstats on the wall. HO would like to speak with someone ASAP about giving him options and potentially running a load calculation on the home.
Complete: 2 systems: worked on DS unit: Goodman Gas Furnace: HO said Unit would come on and go rt back off. At furnace found glow plug not working. Had 120v getting to it. Replaced with new glow plug and unit fired up. Cycled system and unit is working great at this time.
Goodman gas package unit Diagnosed bad gas valve
Installed 3 ton Amana gas package unit with nest gen 3 thermostat
Lennox gas furnace found bad control board