For over 20 years, Apex, NC has known that Comfort First is the company to call for expert heating and air conditioning repair services.
Our Apex, NC reviews show how we hold your heating, cooling and home comfort above all else! See what your neighbors are saying about our HVAC services below.
for Apex, NC
Our Reviews by City
Great service! Professional Representative
Joseph - Apex, NC
I’m extremely pleased with the professional service and maintenance provided by BJ McLeod. Excellent communication and efficient service provided. Everything was checked and serviced in the A/C unit. I’m glad that I now have a Preventative Maintenance Agreement with First Comfort. Thank you very much!
Excellent work Cody and Dennis
Brian - Apex, NC
Fantastic job - quick and efficient, careful and kind. Gave me good info on how to use systems properly. Very professional.
Randy - Apex, NC
Cody and partner were very great. Explained my options and even offered maintenance. Upstairs is cool, wife is cool so all good!
Kristin - Apex, NC
Great job. Done quickly.
Excellent visit. A thorough review of the system.
Wendy - Apex, NC
Nabela - Apex, NC
Carrier straight a.c.. Checked unit for proper operation
Carrier straight a.c. with gas furnace. Found unit low on r410a.
Cleared clogged drain line
Clogged drain and hole in secondary pan
Rheem gas pack bad collector box
Goodman ACS insufficient coolant
Goodman ac......blown 35/capacitor
Clogged drain cleared
Trane low in refrigerant R410-A
Trane gas furnace low voltage short
Serviced Carrier Gas package unit,found bad capacitor & hard start.repaired both checked operation.great at this time.
Noise coming from second floor unit blower motor
Carrier AC second floor 7.5 capacitor blown condenser fan motor
Goodman gas pack checked system found bad dual run capacitor and replaced
Goodman A/C checked system found to be low in refrigerant and added 1 lb R-438 and found valve stim leaking and replaced and cycled system working at this time
Goodman A/C checked system found bad dual run capacitor and replaced
Repaired a carrier gas furnace by replacing the blower motor
Cleared drain line on a trane unit
Diagnosed a frozen evaporator coil
Lennox straight ac with gas heat. Found blower not running due to a bad capacitor. Replaced capacitor and checked system
Repaired a Goodman heat pump by replacing the compressor and recharged system
Repaired a carrier heat pump by replacing the blower motor
Rheem gas furnace blower motor
Repaired a carrier gas furnace by replacing the evaporator coil and recharged system