For over 20 years, Apex, NC has known that Comfort First is the company to call for expert heating and air conditioning repair services.
Our Apex, NC reviews show how we hold your heating, cooling and home comfort above all else! See what your neighbors are saying about our HVAC services below.
for Apex, NC
Our Reviews by City
Odonnell - Apex, NC
I was very happy with the work that Tyler did. He was very courteous and respectful. He even got to know my dog. He even brought her a treat the second day on the job.
Pam - Apex, NC
Thank you for the follow-up to adjust the airflow!
Excellent Customer Service, Honesty & Great Price
Audra - Apex, NC
We highly recommend Comfort First as we have been customers for many years via their maintenance agreement. Today, we had the pleasure of meeting with Bill Smart regarding the purchase/installation of a new unit. His professionalism, customer service and honesty was beyond measure. We will continue our service agreement with Comfort First because they give us peace of mind.
Wonderful, quickand to the point
Richard - Apex, NC
Whole Home Generator Install
KNeill - Apex, NC
Joel and his team were professional and courteous. Install was smooth. Install passed inspection the very next day.
Great Warranty repair of A/C System!
Jim - Apex, NC
Thomas and his team were great! We called American Home Shield when our AC failed in August on a Sunday. We got a call from Comfort First Heating and Cooling Monday morning that they would be out Monday afternoon, fine with us considering we didn’t make the initial call until Sunday afternoon. Thomas and his team actually came earlier which was a nice surprise. They diagnosed the problem quickly and had us back up and running within an hour. I highly recommend Comfort First Heating and Cooling and in particular Thomas!
Great team to work with
Bob - Apex, NC
Joel was extremely knowledgeable and professional. A pleasure to work with. Thoroughly explained the entire process. I would HIGHLY recommend him and his team!!
Neto - Apex, NC
Very pleased with the professional work performed by the team
Jessica - Apex, NC
Donald - Apex, NC
Bradley McLeod was knowledgeable and explained what was wrong with my furnace. He was friendly and pleasant to work with
Rheem gaspack no ac
Rheem gaspack running constantly
Carrier A/C checked system found very dirty condenser coil and cleaned also found systems to be low in refrigerate need to add 2 lb R-22 refrigerate
Carrie gas furnace preformed leak search
Carrier gas furnace replace condenser fan motor
Carrier gas furnace furnace replaced condenser fan motor
Goodman gas furnace found bad compressor
Lennox gas furnace found bad dual run capacitor
Carrier gas furnace replace door run capacitor
Carrier blown capacitor
Rheem hp......replaced cfm blade
Rheem ac no cooling
Complete 1 System Carrier Straight A/C: HO stated outdoor unit was not running and making a loud noise. Found bad cfm. Used 1/4HP 240V cfm. P#:1860. Truck stock. Replaced it. Checked pressures. System is running great st this time.
Complete 3 Systems worked on A Goodman Straight A/C for basement HO stated system was not cooling. Found bad dual cap. Used a 35/5 cap from truck stock. C hecked pressures. System is running great at this time.
Incomplete 1 System Lennox HP Split System 3 Zones. HO stated zone for 2nd floor was not working. Cycled system. Zone damper motor for 2nd floor was not opening. Checked to make sure mother board and tstat were working as they should. They are working properly. Motor damper for 2nd floor is bad. Not opening. Tried to find it but we couldnt. Flexes from supply plenum lead to the attic but we didnt find any access to the attic. There were 3 access doors at the 3rd floor on the wall, we opened them up but didnt have any flexes with motor dampers. Tried 2nd floor. We didnt find any thing. HO said he will find with recent owners and then will call us back. 2nd floor zone still not working.
Complete 2 Systems worked on US Trane Straight A/C System. HO said system was not cooling. Found drain line stopped up. Had to use nitrogen ti clear line. Replaced p trap and made sure drain line was clear. Checked pressures. System is running great at this time.
Goodman package heat pump found bad capacitor
Lennox bsd compressor
Goodman gas furnace performed cooling maintenance
Goodman split heat pump found bad dual run capacitor
Cooling maintenance Amana
Complete 2 Systems worked on US Trane Straight A/C: HO said drain pan was full of water. Found drain line stopped up. Replaced p trap and blew line. Made sure drain line was clear. Checked pressures. System is running great at this tume.
Lennox split heatpump replaced cfm
Trane ac check
Complete: 1System Heil Split HP: HO said he didn’t have 24v getting to the thermostat. At the AH found inline fuse blown and transformer blown. Replaced transformer and fuse. System fired up and working great at this time.