For over 20 years, Broadway, NC has known that Comfort First is the company to call for expert heating and cooling.
Our Broadway, NC reviews show how we hold your heating, cooling and home comfort above all else! Come take a look!
for Broadway, NC
Our Reviews by City
Great Fast Service
Everett - Broadway, NC
Dan - Broadway, NC
Overall great experience.
Wayne - Broadway, NC
We had very good service
Josh - Broadway, NC
1 system EPA cooling maintenance Split Heat pump
Amana split heat pump maintenance
Complete: 1 2Zone system Trane Split Hp: Came to replace indoor txv. Pump system down replaced txv. Leak checked with nitrogen. Pulled vacuum. Released refrigerant. Checked charge and system is working great at this time. inComplete: 1 2Zone system Trane Split Hp: TN said was only blowing hot air and the HP wasn’t coming on. Found system completely flat in refrigerant. Charge with nitrogen and found leak in solder joint at Com
Complete: 1 2Zone system Trane Split Hp: TN said was only blowing hot air and the HP wasn’t coming on. Found system completely flat in refrigerant. Charge with nitrogen and found leak in solder joint at Compressor intake. Repaired leak, nitrogen and bubble tested. Pulled vacuum, no leaks. Added 8lbs or 410a and my low side pressures would no go above 50 ...... reversed refrigerant and system responded great. Went US and found TXV wouldn’t open up. I tapped it and reversed refrigerant a couple of times still wouldn’t open need to order new TXV in the morning. .
Complete: 2 systems worked on Us Unit: Goodman split HP: HO said was working. Checked charge and she was low in 410a charged with 2lbs and Checked SH and SC and system Just Saying!! Working great at this time.
Working on a Tempstar heat pump
Carrier heat pump cooling maintenance
Completed two system cooling maintenance on cattier gas pack and carrier split heat pump
Working on a Goodman heat pump
Complete: 2 System Worked on DS Goodman Heat Pump Split System HO said DS Unit was not cooling to desired temperature, found unit low in refrigerant. Added 3 lbs of 410A and added one can of leak stop. Unit is running great at this time.
Goodman heat pump cooling maintenance
3 ton gas package Goodman
3 ton A.c. / Furnance
4 tons heat pump package Amana
Amana Heat pump cooling maintenance
Amana split heat pump cooling maintenance
Completed two cooling maintenances on American standard split heat pumps
Routine maintenance on an Amana heat pump
Complete: Found pro select Tstat off 4 degrees turning in for warranty. Replaced with honeywell t4. Cycled system and working good at this time.
Trane split heat pump
Amanna dual fual gas pack checked system found CFM not running due to wiring issues and repaired and cycled system working at this time
Working on a Trane heat pump
Bad x13 on carrier split system heatpump
2 lennox heatpump split system checked systems
Amanna dual fual package system completed EPA heating maintenance and cycled system working at this time