Burlington NC – Air Conditioning Repairs & Replacement Options PLUS Heating Services
For over 20 years, Burlington, NC has known that Comfort First is the company to call for expert heating and air conditioning service. We specialize in fixing common AC and heating repair issues in your home. We are experienced at troubleshooting your air conditioning units most common to Burlington (like heat pumps) and we know the typical repair issues because we work here every day. In addition to HVAC repairs – we create customers for life by consistently providing people AND comfort you can count on.
See what your Burlington neighbors are saying about our heating, cooling and home comfort services below!
for Burlington, NC
Our Reviews by City
Great customer service, explained everything
Chavis - Burlington, NC
David - Burlington, NC
Very knowledgeable and extremely professional . Very impress with service.
Tune up Goodman AC
Repair A Trane Heat Pump
Airflow leaks equipment running properly Lennox equipment
Worked on Lennox heat pump -found mouse in blower wheel-check refrigerant charge-had to add refrigerant
Replaced 35/5 mfd capacitor on a Trane Heat Pump
Trane gas black blown 45 dual capacitor
York package unit 1 lb low
Cooling maintenance on a Goodman gas pack
Cooling maintenance on an Amana heat pump
Payne package heat pump completely out of refrigerat preformed leak search and found leaking evaporator coil
Goodman AC blowing dual capacitor
Rheem ac checked system found stopped up primary drain line and cleared and cycled system working at this time
Goodman gas furnace checked system found bad blower motor and replaced
Rheem gas pack no Cooling
Lennox heat pump pack water dripping
Rheem AC ADP coil leaking in attic refrigerant
Trane gas furnace checked system found bad nest thermostat
Trane air handler checked system found float switch in secondary drain pan tripped due to water in secondary drain pan due to stopped up primary drain line and clear and cycled system working at this time
Repla ed accumulator, and evap coil.
Found system low on refrigerant, added 1 lb for optimal cooling.