Burlington NC – Air Conditioning Repairs & Replacement Options PLUS Heating Services
For over 20 years, Burlington, NC has known that Comfort First is the company to call for expert heating and air conditioning service. We specialize in fixing common AC and heating repair issues in your home. We are experienced at troubleshooting your air conditioning units most common to Burlington (like heat pumps) and we know the typical repair issues because we work here every day. In addition to HVAC repairs – we create customers for life by consistently providing people AND comfort you can count on.
See what your Burlington neighbors are saying about our heating, cooling and home comfort services below!
for Burlington, NC
Our Reviews by City
Great customer service, explained everything
Chavis - Burlington, NC
David - Burlington, NC
Very knowledgeable and extremely professional . Very impress with service.
Ruud package heat pump checked system found heat strips not running due to bad sequencer and replaced and cycled system working at this time
Bryant furnace repair
Trane furnace check
Trane gas pack replaced heat exchanger and bunners and cycled system working at this time
Trane gas pack replaced pressure switch and cycled system working at this time
Goodman gas pack completed EPA heating maintenance and cycled system working at this time collected 0
Complete: Came to repair hole in duct work. Found where the hole was in a supply line. However the hole was just in the insulation and hadn’t broken into flex. I taped up hole and everything is working as it should.
Incomplete: 1 System: Trane Gas Package unit HO said that she had been smelling an odor for a few days. GaS LP rolling out and rusted heat exchanger face and 3 rusted burners. Need to replace heat exchanger and 3 burners: Do Not Order until Talks about new system with Beth.
Rheem heat pump completed EPA heating maintenance and cycled system working at this time
Hail gas pack replaced X13 blower motor and cycled system working at this time
Trane gas furnace checked system found dirty flame sencer and cleaned and cycled system working at this time
H e i l gas pack no heat
2 Trane gas furnace completed EPA heating maintenance and cycled system working at this time
Armstrong gas pack replaced heat exchanger and cycled system working at this time
Carrier heat pump checked system found bkower motor not running duebto bad blower relay and replaced also found thermostat not controlling heat strips due to being bad and replaced thermostat and cycled system working at this time
Trane gas pack checked system found to be working at this time
Diagnosed a rust hole on a heat exchanger on a Armstrong gas pack
Repaired a Goodman gas pack by resetting rollout switch
Repaired an Armstrong gas pack by cleaning the burners
Heating maintenance on a Goodman gas pack