For over 20 years, Cameron, NC has known that Comfort First is the company to call for expert heating and cooling.
Our Cameron, NC reviews show how we hold your heating, cooling and home comfort above all else! Come take a look!
for Cameron, NC
Our Reviews by City
Tenant - Cameron, NC
Technician was thorough and explained his diagnosis with possible solutions which may solve the problem.
Great and Polite Service
Billy - Cameron, NC
Heather - Cameron, NC
Renee was very professional and friendly, she made the experience very easy and comfortable, since this was the first time I had to do this! The accuracy and timely manner things were taken care of just BLEW me away!!! I would definitely recommend this company and Renee to ANYBODY needing a heating/cooling system!
Snook - Cameron, NC
Really nice wholesome gentleman
Nicole - Cameron, NC
Nancy - Cameron, NC
BJ came when expected, did a thorough job, and gave us a detailed report when he was done. Exceptionally nice service!
Christine - Cameron, NC
Stress free and knowledgeable
Bill - Cameron, NC
FlounderMan - Cameron, NC
Very good techs at ComfortFirst
The Tech was awesome
Dedeaux - Cameron, NC
The work was done professionally and expeditiously. Great service.
Doryann - Cameron, NC
Mr. David Miles was very kind and knowledgeable, best service that could’ve been provided!
David and Dennis are AWESOME
Meranda - Cameron, NC
Absolutely love David and Dennis as a duo. They corrected issues left from a previous tech. And answered all my questions respectfully. I wont have any other techs come out. Even if it means waiting a couple extra days like i did.
Great service. Very friendly and helpful.
Rebecca - Cameron, NC
They were very helpful and friendly. Willing to work with us and our schedule.
Stewart - Cameron, NC
We've had 3 other people come out from home shield to look at the A/C and he actually found the issue for us. Very nice and helpful.
Debbie - Cameron, NC
Ana - Cameron, NC
Cody was very professional and we are grateful for his service.
Jody - Cameron, NC
Ashley - Cameron, NC
Everything went better than expected. Very happy with service
Routine maintenance on Nordyne heat pump
Working on 2 Goodman heat pumps
Goodman split heat pump no cooling
Rheem split heat pump no heat
Repaired a low voltage short in a Goodman heat pump
Replacing a control board on a Rheem heat pump
Routine maintenance on an Amana heat pump
Goodman gas package unit Diagnosed bad gas valve
Routine maintenance on Goodman heat pump
Working on a Goodman heat pump
Rheem split heat pump. Replaced bad contactor
Replacing a control board on a Lennox heat pump
Trane split heat pump. Repaired leak and recharged system
Amana package heat pump heating maintenance
Working on a Nordyne heat pump
Amana split heat pump heating tune up
Amana split heat pump cooling maintenance
Amana split heat pump heating tune up
Amana split heat pump heating maintenance
Incomplete: 1 System, 2 zones. Second opinion on duct design. Found design bad. The only way to repair is to add an additional zone in the US duct work. Need install dept. to come out and look at it to see what it will take.
Incomplete 1 System 2 system Lennox Split HP: HO said wasn’t cooling or heating. Found condenser not coming on. Found control board power getting to it but not coming out. Bad control board. Lennox Solit Hp (Not under warranty) Part coming from Morrisville be in tomorrow morning. 1/15/20 MN: 14hpx-024-230-17 SN: 1911k23489 Defrost Control Board PN: 16v38 Cost $83.74 ON: 30096155 PO: 56959 $0 Collected
Working on bryant furnaces
Working on goodman heat pump systems.
Eps maintenance on 2 Heil heat pumps
Incomplete: 1 System 2 zone carrier split HP: worked on US zone: TN said there was no heat in very master bedroom and bath. I measured temp coming out of the vents and she had 115 coming out but very little airflow. However rt outside door into the hall and open stairway she had 125 coming out with very heavy air flow. In the attack I noticed that the system looked like it had previously been intended for a 3 zone with the master having its on zone. TN said someone came out and removed 3 zone board bc it wasn’t working. On US zone it has two supply lines one to master and other to hall with 3 bedrooms. The line to hall has a spring adjustable damper. I closed it as far as I could with very little result. The master bedroom rt now doesn’t have a return or seemingly as place with the Tstat would go in there. Need to have someone come out and look at duct work to see what the options are based on system size. Pics in docs. Tried to call HO and got no answer.