For over 20 years, Cameron, NC has known that Comfort First is the company to call for expert heating and cooling.
Our Cameron, NC reviews show how we hold your heating, cooling and home comfort above all else! Come take a look!
for Cameron, NC
Our Reviews by City
Doryann - Cameron, NC
Mr. David Miles was very kind and knowledgeable, best service that could’ve been provided!
David and Dennis are AWESOME
Meranda - Cameron, NC
Absolutely love David and Dennis as a duo. They corrected issues left from a previous tech. And answered all my questions respectfully. I wont have any other techs come out. Even if it means waiting a couple extra days like i did.
Great service. Very friendly and helpful.
Rebecca - Cameron, NC
They were very helpful and friendly. Willing to work with us and our schedule.
Stewart - Cameron, NC
We've had 3 other people come out from home shield to look at the A/C and he actually found the issue for us. Very nice and helpful.
Debbie - Cameron, NC
Ana - Cameron, NC
Cody was very professional and we are grateful for his service.
Jody - Cameron, NC
Ashley - Cameron, NC
Everything went better than expected. Very happy with service
Working on lennox heat pump
Working on goodman wall unit
Working on rheem system
performed diagnostic on honeywell zone system
cleared drain line on Lennox heat pump AC split system zoned
replaced zone damper motor on carrier heat pump AC split system zoned
replaced zone board
replaced emergency drain pan for trane heat pump air handler
replaced contactor on Nordyne heat pump split AC system.
performed diagnostic on zone board
Incomplete: 1 System: Trane Split HP: Came to replace blower motor. When I pulled the motor found a couple of wires hanging and with it being a new board it was difficult to see how the new variable speed motor connected. Called Jimmy he had me str8 wire in a Truck Stock motor so they would at least have AC. Motor came on but was an error on the Tstat. The communication wasn’t acting right due to the motor not being connected to a variable speed. However, the outside unit did come on. Briefly connected guages to check and see if there was refrigerant in the system bc there was oil on the service valves. It seems to have refrigerant but lines weren’t getting cold. Informed HO that David Miles will be back out on Monday per Jimmy to get everything straightened out. Called D&L to see if we had the right board and they confirmed we did but they had emailed Dennis with the wiring diagram. So we need to get that email from Dennis. I also still have the warranty blower motor with me. Left Tru
Worked on Bryant package unit customer has very poor airflow to half the house went underneath house fell into Supply ducts that have fallen off properly secure ductwork customer is now happy
Working on goodman heat pump
Working on a Trane air handler
Routine maintenance on a Carrier heat pump
Complete: two systems: Amana split heat pump: changed out Defrost control board and CFM condenser motor. Started system and checked temperature split system looks good and working great at this time
Provided an estimate for a customer to replace their system that was installed with an oversized unit from another company.
Goodman split heat pump no cooling
Westinghouse split heat pump no cooling
Goodman split heat pump no cooling
Intherm electrical furancenot running
InComplete: 2 Zone Lennox Split HP: HO said upstairs was working great but downstairs seemed to work sometimes and other times not. Found AH filter seemingly not been changed since 2016. Pulled it and needs replacing. Also found downstairs Damper motor sticking. Needs new motor. At the HP we did find the system low in charge. Spoke with HO and she said go ahead and charge it. Added 1lb of 410a. HO is aware that she will have to cover the cost of the filter being it’s a Maintenance issue.
Replaced a run capacitor on a Nordyne electric furnace
7919/complete/down/ goodman hp split/ found system low in r22. Advised to do leak search and tried talking customer into a quote. He wanted to know what we could do for him now. Added 3.5 lbs r22.