For over 20 years, Cameron, NC has known that Comfort First is the company to call for expert heating and cooling.
Our Cameron, NC reviews show how we hold your heating, cooling and home comfort above all else! Come take a look!
for Cameron, NC
Our Reviews by City
David and Dennis are AWESOME
Meranda - Cameron, NC
Absolutely love David and Dennis as a duo. They corrected issues left from a previous tech. And answered all my questions respectfully. I wont have any other techs come out. Even if it means waiting a couple extra days like i did.
Great service. Very friendly and helpful.
Rebecca - Cameron, NC
They were very helpful and friendly. Willing to work with us and our schedule.
Stewart - Cameron, NC
We've had 3 other people come out from home shield to look at the A/C and he actually found the issue for us. Very nice and helpful.
Debbie - Cameron, NC
Ana - Cameron, NC
Cody was very professional and we are grateful for his service.
Jody - Cameron, NC
Ashley - Cameron, NC
Everything went better than expected. Very happy with service
Complete: 3 Systems: Worked on small Upstairs Goodman Split HP: There are two systems upstairs. As you look into attic it’s the unit on far right. Found System not blowing air. At the AH power was coming in as well as 24v from Tstat. Found relay was stuck and bad capacitor. Replaced both and system came on. Also replaced stopped up P-Trap. At the HP (middle of 3 HPs) found system low on refrigerant 2lbs of R22. Added Freon as well as can of leak stop. System is up and running great at this time.
Complete: 1 System: Amana Split HP: HO said unit wasn’t working but was blowing out air. Found HP not on. Flashing error code for compressor trip. Went through the check list as well as checked charge amp draws and capacitor. Everything looked good and was working great. Went to put service door back on and the system tripped. Found Tstat wire going to contactor barely making contact inside wire nut. Stripped it and rewired. Unit started up and we tried to make it trip again and it would not. Cycled system on and off and system is working great at this time.
Therm split h/p not cooling
Performed preventive maintenance on trane heat pumps
Repaired low voltage wiring on trane heat pump.
Diagnosed a leaking condenser coil on a Goodman heat pump
Comfort net Tstat showing h/o how to work
Goodman split hp maintenance
Working on lennox heat pump
Working on amana heat pump
Working on goodman ac
Replacing media filter on a York gas pack
Installing a rheem heat pump split
Maintenance Tune Up on an Amana Heat pump
Goodman split hp
Maintenance on a Goodman heat pump
Mini split maintenance ance and heat pump msintenance
2 system heat pump msintenamces
Changing outdoor fan blade, motor and top of unit due to old age and failure on Goodman unit.
Working on goodman heat pump.
Working on lennox heat pump.
Changing thermostats on 2 Goodman heat pumps
Heating maintenance on 2 Goodman heat pumps
Complete: Amana Gas Furnace Upstairs Closet: Came to install gas valve adapter wire harness. Once installed the unit fired up and is working great at this time.
Amana gas furane no heat