For over 20 years, Cary, NC has known that Comfort First is the company to call for expert heating and air conditioning repair services.
Our Cary, NC reviews show how we hold your heating, cooling and home comfort above all else! See what your neighbors are saying about our services below.
On average homeowners in the Cary NC area pay around $500 – $3,500 to have a whole house generator installed. This price reflects just the installation cost, not the price of the generator itself. Some factors affecting the price include:
- If the site needs to be prepared and concrete poured.
- If a fuel tank needs to be installed or a connection established to existing utilities.
- Any improvements done to the electrical panel, like adding a transfer switch and new wiring.
- Materials and equipment as well as any permits.
For a free estimate on a whole home generator installation, contact the experts at Comfort First Heating & Cooling today!
There are a number of reasons why your air conditioner is running but not cooling your Cary NC home:
- The thermostat set to ON instead of AUTO, and the unit cannot complete a full cooling cycle.
- The air filter is dirty and is therefore either clogging up the air circulation or has frozen the evaporator coil.
- The outdoor unit is dirty and therefore blocking the expelling of hot air from the home.
- The ducts are damaged and leaking cool air before it reaches indoors.
- The condenser fan is broken or the compressor is malfunctioning.
There are a few things to check if your AC is not working:
- See if the indoor or outdoor circuit breaker has tripped. If yes and it continues to trip, you’ll need to contact a technician.
- Inspect the air filter to see if it is dirty. It could be clogging the home’s air circulation.
- Check for any ice on the evaporator coil and refrigerant lines. If so, turn off the unit and let the ice melt. When you turn it back on, if ice forms again you will need to call a technician.
If you are still experiencing issues with your AC, we can help. Contact Comfort First for rapid expert AC repair services!
Some signs that could indicate you need an air conditioner repair near Cary NC include:
Unusual sounds, like rattling, banging or grinding sounds coming from your unit.
- Higher than usual energy bills with no explanation of why.
- The air blowing from the vents is not cool.
- Strange smells from the vents, like musty or electric odors.
- Any leaks or extra moisture coming from your unit.
For a new HVAC system for your Cary NC home, you can expect to pay between $7,000 – $12,000, including new ductwork. If you can use the existing ductwork, the price will reduce by between $2,000 – $3,000. The price is also affected by:
- The size of the home.
- The quality of the unit.
- The energy efficiency of the unit.
for Cary, NC
Our Reviews by City
Air Conditioner Replacement
Michael - Cary, NC
Punctual and efficient service!
Gutierrez - Cary, NC
Performed the work on time, very courteous and provided all pertinent information.
Most sincere A/C technician ever!
Eapen - Cary, NC
Nate was very knowledgeable, took a keen interest in the problem at hand and left me feeling very confident that my problem is in the right hands.
Good price, but Intangibles count too
William - Cary, NC
I was very impressed with the professionalism, courtesy and ability of all associated with my request for a quotation for a replacement HVAC system. I considered 4 vendors and the most comprehensive quote as well as the quote which included significantly more benefits was from your company.
Lynch - Cary, NC
Technician is super friendly and knowledgeable, answered all my questions.
Efficient, smart, nformative and careful
Ursetto - Cary, NC
Professional informative service
Ursetto - Cary, NC
Technicians had great experience, efficient and informative
Wonderful service. Friendly staff.
Sheila - Cary, NC
The entire experience was smooth from start to finish. No one wants to have to replace a furnace right before Christmas, but everyone was so helpful during a very stressful time. Devin and his partner did an excellent job on the install. AJ and Candace provided great service, as well.
Zack - Cary, NC
Great service, personable, answered all my questions patiently:)
ZackH - Cary, NC
Carrier gaspack replaced heatexchanger an inducer motor
Not cooling nordyen hp
Goodman air handler need to replace heat strips
Goodman bad heatstrips
Carrier equipment heating maintenance
Payne heat pump completed EPA heating maintenance and cycled system working at this time
Lennox heat pump completed EPA heating maintenance and cycled system working at this time
PAYNE gaspack no heat
Appollo unit maintenance check
Incomplete 3 Systems woked on 2nd floor Carrier Straight A/C: HO stated system was not cooling. Found system completely out on ref. We spent over 25 mins calling old republic to get autho to perform a leak search, stayed iver the line, lady i was talking with was about to give us the autho code, when suddenly we got transfered to another lady. Then the other lady did not know why we got transfered to her, she transfered me to the autho dept and nobody answered. Jimmy said to perform a leak search. Added a few onces of 410A and nitrogen. Found leak at the evap coil. This is 3 ton Case Coil. System holds 8 lbs of 410A. Called east coast to get part info. P#: CHPF3636B6. Price: $287.32. In Stock. Did not order due to Old Republic having to approve.
Goodman gas furnace replaced case coil
Nordyen hp low charge
Rheem ac replace evap/coil
Lennox replaced zone damper motor and cycled system working at this time
Trane gas furnace found bad capacitor
Comfort maker found leak in evaporator
Rheem case coil and gas furnace instead UV light amd cycled system working at this time
Goodman Gas pack checked system found to be working and maintaining temp at this time
Complete 2 Systems worked on DS Carrier Straight A/C: HO said system was not keeping up. Found system 2 lbs low in ref. Added 2 lbs of R22, and a can of leak seal. Checked pressures. System is running greatbat this time.
Complete 2 Systems worked on DS Lennox Straight A/C: HO stated system was not coming on. Found bad condensate pump. Since it was faulty, it was not letting powet go through to tstat. Used truck stock Proselect condensate pump.
Complete 2 Systems worked on US Ducane Straight A/C: HO stated system was not cooling. Found system not cooling. Added 2 lbs of R22. Added a can of leak seal. Checked pressures. System is running great at this time.
Trane A/C checked system found to be working and maintaining temp at this time
Complete 2 Systems worked on US A/C System. Replaced motor actuator for return flex. Tested. System is running great at this time.
Complete 2 Systems Worked on US Bryant Straight A/C: Came to replace txv. All ref was already out so I had to use new ref. Removed defective txv. Removed drain due to having to pull evap coul out a little. Made sure drain line was clear. Leak tested sysem. Pulled vaccum. Install drain back in place. Added 7 lbs of R22. System is running great at this time.