Whether you need heating, cooling, indoor air quality or another comfort service for your home, Conover, NC, Comfort First is your reliable standby.
Our Conover, NC speak volumes about the high quality heating, cooling and other service we provide–come take a look!
for Conover, NC
Our Reviews by City
Sara - Conover, NC
Kenny was very helpful and explained things really easily. Very happy with this service!
Cardwell - Conover, NC
Quick and easy. Solved the problem quick.
Sandra - Conover, NC
I sure do appreciate Kenney and his excellent service. He is always on time, handles the issue and explains everything to where I can understand what the problem was. You have a customer for life! Thank you sir!
Great Service, Explained everything!
Natalie - Conover, NC
Would definitely recommend to others!
Kenney is great!
Lopez - Conover, NC
I just can’t say enough good things about Kenney! He has become like a friend. He is always so professional but nice and personable as well. I welcome him into my home each time we have a call. He has made the issues we have had not be so bad because of his kindness. A+++
Paul - Conover, NC
Quick and efficient. The repair was explained well.
Checked upstairs system.
Repaired the broken low voltage common wire inside the gas furnace. System is now cooling properly at this time.
Added 1 lb refrigerant and replaced the failed 1 pole contactor. System is now cooling properly at this time.
Added 2 lbs of refrigerant back to system. System is now cooling properly at this time.
Replaced the 45/5uf run capacitor and ordered a special outdoor fan motor which it's failing.
Cleared primary drain trap and line. System is now draining properly.
Replaced 1.5 pole contactor, 45/5uf run capacitor, and added a hard start kit. System is now cooling.
Unclogged primary drain trap and removed water from 2ndary drain pan.
Added 1 lb of r22 back to system. System is now cooling.
Complete 3 systems checked main floor unit and found everything to be running and working properly at this time in cooling mode.
Replaced the failed 50/5uf run capacitor. System is now running and working properly at this time in cooling mode.
Replaced a failed 35/5uf run capacitor. System is now running and working properly at this time in cooling mode.
Diagnosed a bad compressor
Repaired high voltage wire short.
Had a breaker tripping found the the compressor wires were burnt replaced wires unit is working properly at this time
Diagnosed a bad reversing valve on trane heat pump
Searched system and found leaking valve cores. Replaced cores and charged with 6lbs of r22 refrigerant
Diagnosed issue on rheem heat pump