For over 20 years, Dunn, NC has known that Comfort First is the company to call for expert heating and cooling.
Our Dunn, NC reviews show how we hold your heating, cooling and home comfort above all else! Come take a look!
for Dunn, NC
Our Reviews by City
Great Installation Work
Weaver - Dunn, NC
Installers were pleasant and did a great job!
Groover Complete: 1 systems: Trane Split HP: During EPA Maintenance found system low in charge. Informed HO and added 2lbs of r-22 and 1 can of leak stop. Cycled system and system working as it should at this time. Collected $267.50 for 2lbs of r22 via cc sq
Complete: 1 System: EPA Maintenance Goodman Split Heat Pump: Air Handler: Checked Amp Draws on the Blower Motor and Heat strips, checked the capacitor and blower wheel. Inspected Evap coil. Heat Pump: Checked the charge, and the capacitor. Check the Amp draws on the fan and compressor. Cleaned Unit. System looks good and running Great at this time.
Repaired duct on Goodman gas pack
Found bad inducer motor on dual fuel package unit
performed heating maintenance on Goodman heat pump AC split system upper and lower.
Found bad inducer motor on nuton gas pack
Working on a goodman gaspack
Found Goodman split heat pump out of Freon
Replaced heat exchanger on Goodman gas pack
Replaced compressor on Trane split heat pump
Replaced compressor variable speed CFM and CFM control board on Trane split heat pump
Replaced evaporator coil on Goodman split heat pump
Gas pack found blower motor spinning backwards causing lack of air flow
Just finished up installing a new 2.0 ton Amana Split Heat Pump. Upsized a return from 14 inch flex to 16 in flex.
Provided an estimate for the customers to replace their split heat pump. We will be installing the system this week.
Complete: 2 Systems: Worked on Upstairs Unit: Goodman Split HP: HO said feels like hot air blowing when in cool mode. At HP found reversing valve not energized. Power was coming into and out of board. Then checked solenoid and found one of the wires had come loose. Placed wire back on and reversing valve energized. Cycled system on and off and system is working great at this time. $0 Collected
Working on goodman gaspack
Heating maintenance on a Goodman package heat pump
Heating maintenance on a Amana gas pack
Heating maintenance on 2 Amana heat pumps
Working on goodman package heat pump.
Found a bad cap and nonprogrammable thermostat on a Gas Pack
Working on a Split system Goodman Hp that had a bad capacitor on blower motor
Just finished installing a 3.5 ton Amana package heat pump.
Meeting with a customer to discuss replacing his packaged heat pump.