Local HVAC Services in Durham NC
You may have seen the Comfort First Heating & Cooling vans in the Durham, NC area driving to or from a heating service or air conditioning repair job. We’re the company trusted all over North Carolina for five star service. We can provide an enormous variety of benefits from your home and your family, including increased comfort, energy savings and improved indoor air quality.
Your Air Conditioning and Heating Comfort is our Top Priority.
See what your Durham neighbors are saying about our service below and call us locally at (919) 985-7660.
for Durham, NC
Our Reviews by City
Busacco - Durham, NC
Your workers were efficient, polite and thorough.
Jennifer - Durham, NC
Project manager was very thorough and explained in detail the process of a installing a new hvac system in our home.
Serviceman was knowledgeable and professional.
Valrie - Durham, NC
Great customer service from technician.
Great service and service person
Eugene - Durham, NC
Prompt, attention to detail was Cody's mission.
Julius - Durham, NC
Anna - Durham, NC
Wonderfull, very insightful, answered all my questions, great manners.
Jeanne - Durham, NC
Wanda - Durham, NC
Patrick - Durham, NC
Seriously. Really great service
Great knowledgeable service guy
Robert - Durham, NC
Diagnosed a leaking evaporator coil on a trane case coil
Cooling maintenance on a trane heat pump
Cooling maintenance on a carrier heat pump
Noise from first floor unit no issues inducer motor question
System not working call was cancelled
System not working call cancelled
Cooling tune-up Rheem unit approximately 13 years old
Cooling tune-up Trane AC
Cooling maintenance on 2 heil ac units
Cooling maintenance on 2 Goodman heat pumps
Goodman AC cooling tune up
Rheem ac tune up
Trane ac and Trand gas pack completed cooling maintenance on system and cycled system working at this time
Just finished replacing 15 6 in supply runs and a 16 in & 14 in return.
Goodman A/C recharged system with 5 lb R438A
Preseason tune up on Goodman unit
Carrier heat pump checked system found but common wire at capacitor due to lose wiring connection and repair also found bad nest thermostat
Working with homeowners to design and install a new HVAC and duct system.
Trane gas pack replaced gas valve and cycled system working at this time
Trane equipment 30 years old cooling tune up
Heating and Cooling tune-up Rheem unit
Goodman ac checked system found system to be pumped down with no pressure on line set need to remove current charge in system pull vacuum and recharge system with 5 lb R-22 to properly diagnose system
Trane gas pack replaced flame sencer and found bad gas valve due to high inlet gas pressure
Ruud gas pack checked system found open pressure switch due to stopped up vacuum tub and cleared and cycled system working at this time
Goodman A/C completed cooling maintenance on system and cycled system working at this time
Carrier gas pack and carrier A/C completed cooling maintenance and found bad dual run capacitor for A/C and replaced also found bad run capacitor for blower on gas pack and replaced and cycled system working at this
Goodman equipment coolintune-ups
Goodman heat pumps no heat second floor leaking evaporator coil
Goodman package heat pump checked system found blower motor not running due to lose wiring connection and repaired