Your heating and cooling and overall comfort in Garner, NC is important to Comfort First.
See how we show it in every service call and visit in Garner, NC by taking a look at our reviews!
for Garner, NC
Our Reviews by City
Veronica - Garner, NC
Macalam - Garner, NC
Griffiths - Garner, NC
Eval of heat pump malfunction
Vicki - Garner, NC
Very thorough, honest, and personable
Potts - Garner, NC
Appreciate the tech sent. Thomas was savvy and professional. He made sure all was in good working order before leaving Great experience
Mr - Garner, NC
Jenna - Garner, NC
Very knowledgeable, friendly, helpful, went above and beyond and helped me with another issue with another company (propane company)
Great techs, great service
Justin - Garner, NC
Fixed a 3 yr recurring issue in an hour.
Jayne - Garner, NC
The hvac men were very professional, polite and kind. They were able to get a new part earlier than anticipated. They arrived earlier than scheduled time which was great for me. Went right to work and installed a new compressor.
Complete 1 system Lennox AC/ Gas Furnace. 2 Zones. HO said no air coming out upstairs. Found broken power damper to US unit. Need to order new damper. From East Coast
Goodman straight a.c. split. Diagnosed leaking case coil
Goodman split heat replaced bad thermostat and added refrigerant
Lennox split heat pump cooling maintenance
Lennox split heat pump. Replaced faulty condenser fan motor
Goodman straight a.c.. Replaced leaking case coil
Goodman straight a.c. cooling maintenance
Goodman gas package unit Added refrigerant
Carrier split heat pump. Diagnosed leaking evaporator coil
Comfort maker split heat pump. Replaced bad dual capacitor
Goodman split heat pump. Installed hard start to help compressor start
Goodman split heat pump. Installed uv light kit in system
Trane split heat pump. Replaced bad condenser fan motor
Carrier split heat pump. Diagnosed locked up compressor
Trane split heat pump. Diagnosed leaking evaporator coil
Goodman split heatpump preformed cooling maintenance
Trane split Heat pump replaced contactor on condenser unit also replaced blower relay on air handler
1 Trane split heat pump found bad compressor 1-Goodman split heat pump found bad evaporator coil
Complete: 1System: Amana Split HP: HO said unit wouldn’t come on outside. Found blown fuse under the house. Replaced fuse and looked for short. Found 5of6 Tstat wire coming from Tstat into AH nicked about 3” up in same area. Cut out and rewired. Checked charge and system is on and running as it should at this time.