Your heating and cooling and overall comfort in Garner, NC is important to Comfort First.
See how we show it in every service call and visit in Garner, NC by taking a look at our reviews!
for Garner, NC
Our Reviews by City
Mr - Garner, NC
Jenna - Garner, NC
Very knowledgeable, friendly, helpful, went above and beyond and helped me with another issue with another company (propane company)
Great techs, great service
Justin - Garner, NC
Fixed a 3 yr recurring issue in an hour.
Jayne - Garner, NC
The hvac men were very professional, polite and kind. They were able to get a new part earlier than anticipated. They arrived earlier than scheduled time which was great for me. Went right to work and installed a new compressor.
Repaired a interferem air handler by replacing 2relays
Diagnosed a bad condenser fan motor on Payne heat pump
Diagnosed a bad condenser fan motor on a carrier gas pack
Repaired a trane heat pump by replacing p trap and clearing drain line
Lennox air handler with 3 zones checked system found up stairs zone not geting air flow due to zone damper not opening due to had zone damper motor need to replace zone damper motor
Trane A/C replaced compressor bi flow drier capacitor and recharged system with 7 lb R-22 and cycled system working at this time
Goodman low in R22 refrigerant
Up stairs Carrier heat pump checked system found to be low in refrigerant and added 1 lb R-410 to system and cycled system working at this time
Down stairs Carrier heat pump checked system found to be low in refrigerant and added 2 lb R-410 to system and cycled system working at this time
Trane a/c checked system found compressor not pump due to being bad need to replace compressor
Trane heat pump checked system found stopped up primary drain line and cleared
Trane air handle replaced blower motor AMD adjusted sub cooling
Repaired a Goodman heat pump by replacing the capacitor
Ducane gas package unit. Found extremely dirty air filters causing an air restriction making the unit not cool effectively
We installed a 2 ton Goodman heat pump with airhandler with 5 kw heat kit
Working on a carrier heat pump
York heat pump checked system found compressor and fan motor not running due to bad dual run capacitor and replaced and cycled system working at this time
Goodman heat pump checked system found compressor not starting and added hard start to system and cycled system working at this time
Trane hear pump checked system found to be low in refrigerant and found leaking valve stim and replaced and cycled 4 lb R-410 to system and cycled system working at this time