Your heating and cooling and overall comfort in Gibsonville, NC is important to Comfort First.
See how we show it in every service call and vist in Gibsonville, NC by taking a look at our reviews!
for Gibsonville, NC
Our Reviews by City
Awesome service, let me know what was needed
Cathy - Gibsonville, NC
Very good service let me know what was wrong was very straightforward and kind. Brought my dogs some treats which they are very happy. We all are.
Great service. Quick and knowledgeable.
Phil Thompson - Gibsonville, NC
Billy saw what the problem was in 5 minutes or less and even talked to me as he worked to explain what happened.
Eddie - Gibsonville, NC
Very helpful with recommendations
Complete 2 Systems Worked on DS Amana Straight A/C: EPA Cooling Maintennace: Checked thermostat and air filter. Checked blower motor amp draw. Checked all wiring. Inpected evap coil. Made sure drain line was clear. Checked cfm and compressor amp draws. Checked all wiring at condenser. Checked dual run cap. Checked pressures. Cleaned condenser coil. System is running great at this time.
Rheem gas pack checked system found zone system unwired and not in operation casing temp to be higher on second floor need to added thermostat and rewire zone system
Trane heat pump replaced Indoor TXV and pulled vacuum and added 1 lb R-410 refrigerate and cycled system working at this time
Trane heat pump amd air handler checked system found bad indoor TXV need to replace indoor TXV
Payne gaspack...evap/coil leaking
Carrier gaspack low refrigerant
Carrier gaspack low charge r22
Lennox ac check
Work on Amana gas furnace
Worked on Goodman heat pump
Worked on Carrier gas furnace
Working on Amana gas furnace
Worked on Rheem heat pump
Worked on air conditioner
Worked on Trane air conditioner
No one home need to reschedule when some one can be available
Airease...hp bad compressor
Trane gas pack checked system found to be working and maintaining temperature at this time
Lennox ac completed cooling maintenance and cycled system working at this time
Tempstar heat pump package Unit no heat
Heating tune up...
York Furnace no heat
Goodman furnace....flame senor dirty
Incomplete: LG Mini split: Wasn’t blowing hot air. At the Outdoor unit found compressor terminals unattached from top of compressor. Needs new compressor. Need to order in the AM. Talked to HOs mother and she is ok with Beth giving her a call about options towards a new system. Pics in Docs
Carrier gas furnace checked system found bad blower motor and replaced and cycled system working at this time