Expert Heating & Air Conditioning Services in Greensboro, NC
Comfort First Heating & Cooling has got your HVAC basics in Greensboro, NC covered and more! From your air conditioning system to your attic insulation to your whole home generator needs and beyond, our experts can help with anything you need. You can not only count on our professional services but our people and our company as a whole.
Your Air Conditioning and Heating Comfort is our Top Priority.
See what your Greensboro neighbors are saying about our service below or call us to schedule your next service.
for Greensboro, NC
Our Reviews by City
Vikas - Greensboro, NC
Karen - Greensboro, NC
Bradley McLeod delivered wonderful customer service. He was professional and courteous and took care of what we needed very quickly!
Kikawa - Greensboro, NC
Answered all my questions and was very timely. Great customer service
HappyCamper - Greensboro, NC
Tony came and got us ready for winter! Thankful for his knowledge and service.
Lynn - Greensboro, NC
Professional, great personality and very good job!
Ronda - Greensboro, NC
Excellent customer service
Jason - Greensboro, NC
Andy did a great job to narrow down what was causing my unit not to work. Grant it’s 100 degrees and I know they just want to get home. He was very thoughtful and willingness to find out why it stopped working in the first place was a great welcome. The unit started working before even looking at it and both of us were in awe of why. But Andy didn’t just want to leave without going thru every possible reason of why it happened in the first place. Most people would have said “I don’t know what to tell you?” But he insisted we figure it out. Eventually we found the culprit and was quick to get it up and going. Thanks for your help. Andy did an excellent job!
Marilyn - Greensboro, NC
Glad i only had to wait two days for service.
James - Greensboro, NC
Great Service! Great Tech!
Roger - Greensboro, NC
Billy did a great job, and was very professional and personable. I was highly impressed with the speed in which he replaced the capacitor.
Trane gas pack checked system found tripped roll out switch due to rusted through heat exchanger need to replace roll out switch and heat exchanger
Goodman equipment......no problems
Lennox no heat...heat module bad...
Trane gas furnace replaced pilot tubing and cycled system working at this time
Goodman gas furnace replaced draft inducer assembly and cycled system working at this time
Lennox 90% gas furnace checked system found drian one not glued properly and drian under home reglued drain and cycled system working at this time
Goodman gas furnace checked system found dirty flame sencer and cleaned and cycled system working at this time
Working on 80% Trane gas furance another great day at working for your heating and ac needs call comfort first htg. & Cooling 919-777-7777
Work on Apollo system found transformer bad replace system is up and running customer is happy
Apollo checked system found bad transformer and replaced and cycled system working at this time
Trane heat pump checked system found to be working and maintaining temperature at the same time
Working on Trane split heat pump system check out great no problems at this time
Just finished installing a 2.0 ton Split Heat Pump.
Incomplete: Wrong Part: Spoke with HO and she was really nice about it. Called lennox and they do have one in stock. Should arrive Monday morning. Call before traveling to pick it up to make sure it’s there. Lennox Gas Furnace MN: G20RQ3E-75-5
Bryant gas furnace checked system found bad draft induce motor need to replace draft induce motor
Armstrong heat pump completed heat maintenance and cycled system working at this time
Trane gas furnace completed EPA heating maintenance and cycled system working at this time
Icp water furnace replaced water pump
ICP water furnace replaced water pump and bleed air out of system and cycled system working at this time
Goodman gas furnace checked system found bad draft induce motor need to replace draft induce motor
Diagnosed a bad inducer motor on a Goodman
Trane gas furnace replaced gas valve and found pilot tub was to short after repairs need to replace pilot tib
Trane gas furnace replace gas valve
Trane gas package unit heating maintenance
Bryant gas furnace. Repaired leakage from around inducer motor assembly.
Trane split heat pump. Diagnosed register sweating
Trane split heat pump Diagnosed dirty Evap coil
Trane split heat pump. Sealed leaking ductwork
Goodman gas furnace. Replaced broken hot surface igniter
(On Call Tech) Incomplete: Lennox Gas Furnace: Unit would not come on. When I reset unit heard the igniter try and arc. But nothing else. Had power coming into the board but not coming out. Tried universal board on truck but could not match up. Need to order replacement Lennox control board on Monday: