Expert Heating & Air Conditioning Services in Greensboro, NC
Comfort First Heating & Cooling has got your HVAC basics in Greensboro, NC covered and more! From your air conditioning system to your attic insulation to your whole home generator needs and beyond, our experts can help with anything you need. You can not only count on our professional services but our people and our company as a whole.
Your air conditioner may be running but not cooling your Greensboro, NC home because:
- You air conditioner has a refrigerant leak
- Your air filter is clogged
- Your thermostat is set incorrectly
If you notice that your air conditioner is running but not cooling, you should check your thermostat to ensure that it is set to AUTO not ON. If you reset your thermostat and replace your air filter and your air conditioner is still not cooling, your air conditioner may have a more severe issue. To get your air conditioner repaired, call us today.
The average cost to repair a home air conditioner or furnace system in Greensboro, NC is about $350-$600. The overall cost of the repair can vary depending on the type of repair that is required and the severity of the repair. In some instances, a repair may require replacement components, causing the price of the repair to increase. Additionally, repairs will generally be more expensive after hours and on the weekends. To find out more about getting your home air conditioner repaired, give us a call today.
A few signs you should replace your central air conditioning system rather than repair it in your Greensboro, NC home are:
- Your air conditioner is over 10 years old
- Your air conditioner requires many repairs
- Your air conditioner no longer cools effectively
Another sign you should replace your central air conditioning system is if your energy bills have increased. As your central air conditioner ages and becomes less efficient, it will cost you more on energy and repairs each year. To get your central air conditioner repaired, contact us today.
A whole home generator typically costs around $1,500-$7,500 in Greensboro, NC. Some things that can affect the price are:
- The size of your house
- The size of the generator you will need
- The type of generator you want installed
The size of the generator you need will depend largely on the amount of appliances you need powered in your home. It is always best to round up in size with generators, as a generator that is too small for your home will not last as long. To get a whole home generator installed, call us today.
Your Air Conditioning and Heating Comfort is our Top Priority.
See what your Greensboro neighbors are saying about our service below or call us to schedule your next service.
for Greensboro, NC
Our Reviews by City
Kathy - Greensboro, NC
First class from beginning to install!
Bridget - Greensboro, NC
Very nice, showed me what he did, quick.
Stansfield - Greensboro, NC
Brad - Greensboro, NC
Billy did a fantastic job - took time to explain everything to me. Really appreciate the great service!!
Fabulous, Prompt Service!
Jennifer - Greensboro, NC
My technician Bill was very friendly and knowledgeable. He took the time to explain the workings of my furnace, what he was looking for and how to fix it.
Pam - Greensboro, NC
Billy was great, explained everything to me in terms I could understand. He was polite & very professional. I was very impressed!
Todd - Greensboro, NC
Everyone was professional and knowledgeable.
Very good service
Earl - Greensboro, NC
Arrived on time. Timely work. Good cleanup.
Sandra - Greensboro, NC
Billy and Eric were professional and personable. They fixed the thermostat issue and made sure everything was working correctly. They explained how to work the thermostat and asked if I had any questions. Thank you! Billy and Eric for excellent work and customer service.
Broderick - Greensboro, NC
Billy and Eric did a great job at identifying the issue with our hvac system and came very early in the time window given (huge convenience). Overall a great experience.
Tempstar completed EPA heating maintenance and cycled system working at this time
Rheem A/C and case coil with gas furnace checked system found systwm not drining due to no vent in primmy drain line and repired
Rheem furnace heating maintenance
Complete 1 System Lennox Gas Pak EPA Heating Maintenance: cycled system. Checked tstat and air filter. Checked electrical connections. Inspected evap coil. No CO2. Burners are clean. Cleaned All safety switches are on great condition. Checked draft motor amp draws and cap. System is running great at this time.
Amanna gas pack completed EPA heating maintenance and cycled system working at this time
Whirlpool A/C checked system found run wire not connected causing compressor not to run and reconnected and cycled system working at this time
Complete 1 System ThermoPride Straight A/C: Checked thermostat and air filters. Checked blower motor amp draw. Checked run cap. Checked all wiring. Inpected evap coil. Made sure drain line was clear. Checked cfm and compressor amp draws. Checked all wiring at condenser. Checked dual run cap. Checked pressures. Cleaned condenser coil. System is running great at this time.
Complete 1 System Goodman Gas Furnace: EPA Heating Maintenance: cycled system. Hecked air filter. Checked blower motor amp draws. Checked run Cap. Checked electrical wiring. Cleaned flame rod. Inspected heat exchanger. Tighten up screws. Inspected burners. System is running great at this time.
Goodman furnace repired wire for condensation pump and installed co deoctor in master bedroom
Goodman heat pump checked system found to be low in refrigerate and added 2 lb R-410 to system and cycled system working at this time
Carrier replaced wiring harness and transformer and cycled system working at this time
Comfortmaker heat pump checked system found blown 30 amps fuses at service disconnect due to grounded compressor need ro replace compressor
Carrier checked system found stopped up primmy drain line and cleared and cycled system working at this time
Carrier air handle replaced blower mootr and found high voltage short need ro replace heat strips
Trane A/C checked system found to be working and maintaining temp at this
Lennox A/C checked system found major air laek at case coil and repaired also found system to be low in refrigerate and added 2 lb R-410 A and cycled system working at this time
Whirlpool A/C replaced compressor and recharged system with 6 ɔn R-438 and cycled system working at this time
Goodman A/C checked system found bad thermostat and replaced and cycled system working at this time
Whirlpool A/C checked system found bad compressor need to replace compressor
Trane heat pump checked duct system
Goodman case coil measured and sized new case coil
Carrier A/C checked system found bad dual run capacitor and replaced with truck stock capacitor and cycled system working at this time
Payne Air handler checked system found bad contral board need to replace blower contral board
Goodman heat pump checked system found to be low in refrigerate and added 3 lb R-22 to system and cycled system working at this time
York equipment cooling maintenance
Lennox A/C checked system found shorted wire going to condenser motor and repired also found bad dual run capacitor and replaced and found system to be low in refrigerate and added 2 lb R-410 refrigerate to system and cycled system working at this time
Trane A/C and heat pump checked system found bad 70 amp breaker in main pannel box need to get election to replace
ICP A/C replaced CFM amd CFB amd cycled system working at this time