Your heating and cooling and overall comfort in Haw River, NC is important to Comfort First.
See how we show it in every service call and vist in Haw River, NC by taking a look at our reviews!
for Haw River, NC
Our Reviews by City
Complete 1 System worked a Trane straight A/C system HO said system was blowing hot air when on cool mode. Found drain pan full of water which it tripped wet safety switch. Got all the water out of drain pan, replaced P Trap. Checked refrigerant charge and split temp. (17 dif). System looks good and running great at this time.
Trane ac.... not cooling
Trane hp...replaced condenser motor
Trane ac.. Condenser motor bad.....
Trane...gas pack....no heat/exchanger bad
Goodman gas furnace checked system found dirty flame sencer and cleaned and cycled system working at this time
Goodman gas furnace replaced igniter and cycled system working at this time
Goodman gas furnace checked system found ignitor not properly igniting furnace need to replace ignitor
Goodman fur...bad gas valve
Payne gas furnace completed heating maintenance and cycled system working at this time
Trane heat pump checked system found cfm not running due to bad dual run capacitor and replaced with 35/5 capacitor and cycled system working at this time
Lennox heat pump checked system found to be low in refrigerant and preferred leak search and found leaking condenser coil
Repair of Lennox Heat Pump
Payne gas furnace completed heating maintenance
Installing a compressor on a heat pump system