Your heating and cooling and overall comfort in Holly Springs, NC is important to Comfort First.
See how we show it in every service call and visit in Holly Springs, NC by taking a look at our reviews!
for Holly Springs, NC
Our Reviews by City
Great and fast service
Sims - Holly Springs, NC
Kirsten - Holly Springs, NC
I was incredibly impressed by the entire work crew. They worked hard, were super polite, and got the job done without issue. A+++
Great fast service
Robert - Holly Springs, NC
Shawn did a great job and was very helpful with information. Up and running very quickly.
Tony - Holly Springs, NC
Comfort First did an amazing job getting my HVAC system up and running. Awesome service.
Sandra - Holly Springs, NC
Kelli is knowledgeable about all aspects of HVAC systems and presents the information well. I really got an education today! She is friendly and professional. I am very impressed with her and your company. I am unable to rate the cost with stars as there is no comparison. The pricing of the system as presented with everything included seems fair. Highly recommend your company and Kelli!!!
Shelly - Holly Springs, NC
Service is awesome as always. They come when they say they will and they are the nicest people ever.
Trane furnace no cooling bad control board
Trane ac blown blower capacitor
Payne equipment bad thermostat
Train gas furnace found unit 2 pounds low on our 22
Carrier gas furnace found water and drain pan
Complete 2 Systems worked on DS Goodman Split System. Came to replace compressor. When arrived, I had to wait more than 15 mins for HO to get home. Called office to ask while I would wait, to collect payment. Waited more than 10 mins, called back office to check with them, nobody answered. Asked wife to call her husband to make sure payement was collected, nobody Called him. I had to collect payment. Waited almost an hour to get started with job. Reason why it took too long. Removed old comp. installed new one in. Replaced filter dryer. Had to repipe lines to compressor. Added 7 lbs of 438A. Office will need to collect for the additional 1 lbs. replaced dual cap. Used a 50/5 dual cap. Checked pressures. System is running great at this time.
York A/C replaced service valve and cycled system working at this time
Goodman Heat pump checked system found bad coresence need to replace
Complete two systems worked on downstairs Goodman split heat pump; homeowner said that the system just stopped cooling. Found downstairs heat pump not coming on. Found contactor and wires burnt up. Replace contactor repaired wires and check the charge. System is working great at this time.
Amanna A/C replaced case coil and recharge system with 3 lb R-410 and cycled system working at this time
York A/C checked system found service valve leaking need ro replace 3/4 and 3/8 services valve
Working on a Goodman heat pump
Train gas furnace found bad contactor and capacitor
Goodman gas furnace replace CFM and control board
Trane ac repair
Goodman ac check
Goodman split heat pump. Replaced bad dual capacitor and cleared drain lone
Carrier split heat pump Replaced leaking evaporator coil
Goodman split straight a.c.. Added refrigerant
Lennox split heat pump. Repaired sticking damper motor