Your heating and cooling and overall comfort in Holly Springs, NC is important to Comfort First.
See how we show it in every service call and visit in Holly Springs, NC by taking a look at our reviews!
for Holly Springs, NC
Our Reviews by City
Great fast service
Robert - Holly Springs, NC
Shawn did a great job and was very helpful with information. Up and running very quickly.
Tony - Holly Springs, NC
Comfort First did an amazing job getting my HVAC system up and running. Awesome service.
Sandra - Holly Springs, NC
Kelli is knowledgeable about all aspects of HVAC systems and presents the information well. I really got an education today! She is friendly and professional. I am very impressed with her and your company. I am unable to rate the cost with stars as there is no comparison. The pricing of the system as presented with everything included seems fair. Highly recommend your company and Kelli!!!
Shelly - Holly Springs, NC
Service is awesome as always. They come when they say they will and they are the nicest people ever.
Carrier A/C AMD heat pump checked both system and found both to be working and maintaining temperature at this time
Carrier split heat pump. Added refrigerant
Westinghouse straight a.c. Replaced leaking case coil and recharged system
Trane straight a.c. Replaced leaking case coil and recharged system
Carrier split system
Lennox low on charge leak dye test
Puron split heatpump charged system with 3lbs of 410a
Trane gas furnace found vacuum tube going to pressure switch clogged
Goodman heat pump adjusted sensor on drain pump
2- system Trane gaspack and heat pump cooling maintenance
Lennox split heat pump Replaced bad outdoor txv
Lennox heat pump replaced TXV recharged system. Cycled system everything working
Carrier gas package unit cooling maintenance
Trane split heat pump. Diagnosed leak in the condenser
Carrier straight a.c. cooling maintenance
Amana gas package unit cooling maintenance
Goodman gas furnace. Found insulation sucked up against blower. Cleared insulation
Lennox split heat pump. Diagnosed bad outdoor txv
EPA maintenance on 2 Trane ac systems