Your heating and cooling and overall comfort in Hope Mills, NC is important to Comfort First.
See how we show it in every service call and vist in Hope Mills, NC by taking a look at our reviews!
for Hope Mills, NC
Our Reviews by City
Denise - Hope Mills, NC
Brianna - Hope Mills, NC
Plotnick - Hope Mills, NC
Assigned Comfort First by my warranty service. Prompt and professional service. David took time to explain the issue, repairs and answer questions.
great guy, very knowledgable
Sides - Hope Mills, NC
I would recommend this company and Thomas to anyone
Joe - Hope Mills, NC
Quick and on point
Great service experience with Comfort First heating and cooling.
Lester - Hope Mills, NC
Trust worthy and professional company. Technician was very professional and thorough. He explained everything he was doing as well as what he found. I am very satisfied with my service experience.
Great service, awes
Kimara White - Hope Mills, NC
Cody Smithwick did an awesome job, very professional and knowledgeable. ☺️
Awesome resolve and cortious.
Melinda - Hope Mills, NC
Cody came and listened to our problem and in no time resolved the issue. Awesome.
Dunham - Hope Mills, NC
Great company and great customer service I am very happy and the house feels so much better thank you!
Natasha - Hope Mills, NC
He was awesome and took his time explaining things and answering questions.
Corinthia - Hope Mills, NC
Our problem was fixed quick and the gentlemen was very nice and professional.
Maria & Fil
Maria - Hope Mills, NC
We were very pleased with your representative, very courteous and knowledgeable, with the ability to explain in detail all the technicalities. She is certainly a great asset to your company. It was a pleasure and we will follow up for an installation date. Thank you!
Complete: 2 Systems: Worked on Downstairs Unit: Trane Split Heat Pump: HO said it just stopped working and sound outside as if it was trying to run but would then click out. Opened HP and saw swelling on the capacitor. Changed Cap and system and Charge looks good and running great at this time!
Complete: 2 Systems: Worked on Upstairs Unit: Payne Split HP (NO DATA PLATE) r-22 refrigerant. Homeowner said it would work for a little while and then it would start blowing hot air turn the system off turn it back on nothing would happen couple days go by turn it back on and it would start working again. At the heat pump checked pressures pressures looked good checked the amp drawls the amp drawls looked OK. Difficult to know exactly where it needed to be. Check the capacitor and the common wire from the contactor to the capacitor was barely touching And the capacitor was bad. Replaced capacitor and tightened wires. 20° temperature split upstairs. System looks good and running great at this time!
Performed leak search on Goodman heat pump AC
Performed diagnostic on Goodman heat pump AC
Performed preventive maintenance on Goodman heat pump AC
Performed preventive maintenance on Amana heat pump AC
Replaced condenser fan blade on Goodman heat pump AC
Replaced condenser fan motor on Lennox heat pump AC
Performed diagnostic on Goodman heat pump zone board
Completed load calculation for a customer who is intrested in having their system replaced and getting Duke Energy rebates.
Air Handler: Checked Thermostat and Capacitor, Filters and Amp Draws on the Blower Motor, Inspected Evap coil. Replaced P-Trap, checked condensate line. Heat Pump: Checked the charge, and the capacitor. Check the Amp draws on the fan and compressor. Cleaned Unit. Washed Coils
Completed load calculation for a home warranty customer to have their system replaced.
Replaced compressor on Payne split heat pump
Complete: 1 System: Goodman Split HP: Tenant said unit was working intermittently blowing out cold air. At HP found contactor pitting and melted plastic keeping contactor from making connection all the time. Replaced contactor checked refrigerant and system is working great at this time.
Complete: 1 Systems: Goodman Split Heat Pump: No Cool air, checked freon and it was about 3lbs low. Performed leak search and could not find the leak. Found her return completely stopped up. Pulled filter told her she needed to change it ASAP. Charged with 3lbs of R22. System looks good and running great at this time.
Added r22 refrigerant to Goodman heat pump
Added r22 refrigerant to Goodman heat pump
Replaced thermostat on Goodman heat pump
Replaced thermostat wire and transformer on Goodman heat pump
Completed load calculation for a customer to replace their 2 systems. We are installing then next week.
Provided an estimate for a customer to replace their package unit. We will be putting the system in next week.
Bryant split heat pump. Replaced faulty defrost board and contactor. Found and repaired low voltage short
Goodman heat pump split system. Found grounded compressor causing breaker to trip
Replaced 30 amp breaker on Goodman heat pump disconnect