Your heating and cooling and overall comfort in Hope Mills, NC is important to Comfort First.
See how we show it in every service call and vist in Hope Mills, NC by taking a look at our reviews!
for Hope Mills, NC
Our Reviews by City
Mcgowan - Hope Mills, NC
Benny - Hope Mills, NC
Totally worth the trip
Denise - Hope Mills, NC
Brianna - Hope Mills, NC
Plotnick - Hope Mills, NC
Assigned Comfort First by my warranty service. Prompt and professional service. David took time to explain the issue, repairs and answer questions.
great guy, very knowledgable
Sides - Hope Mills, NC
I would recommend this company and Thomas to anyone
Joe - Hope Mills, NC
Quick and on point
Great service experience with Comfort First heating and cooling.
Lester - Hope Mills, NC
Trust worthy and professional company. Technician was very professional and thorough. He explained everything he was doing as well as what he found. I am very satisfied with my service experience.
Great service, awes
Kimara White - Hope Mills, NC
Cody Smithwick did an awesome job, very professional and knowledgeable. ☺️
Awesome resolve and cortious.
Melinda - Hope Mills, NC
Cody came and listened to our problem and in no time resolved the issue. Awesome.
Dunham - Hope Mills, NC
Great company and great customer service I am very happy and the house feels so much better thank you!
Natasha - Hope Mills, NC
He was awesome and took his time explaining things and answering questions.
Corinthia - Hope Mills, NC
Our problem was fixed quick and the gentlemen was very nice and professional.
Maria & Fil
Maria - Hope Mills, NC
We were very pleased with your representative, very courteous and knowledgeable, with the ability to explain in detail all the technicalities. She is certainly a great asset to your company. It was a pleasure and we will follow up for an installation date. Thank you!
Worked on Goodman heat pump replace compressor capacitor filter line drier recharge System test operation running
Replace condensing fan motor 50 + 5 microfarad capacitor repaired burnt wires tested operation system running properly
Worked on Trane heat pump installed new compressor new capacitor and new filter drier recharge system tested operation system running properly
Complete two systems upper installed new contactor last month customer had ants in the contactor cleaned it out working properly
Installed new compressor pressure test pulled vacuum recharge system running properly
Worked on Goodman heat pump cleared clogged drain line replaced P-trap system working properly
Worked on Trane heat pump replace the evaporator coil
Complete: 1 System: In Closet AH was leaking water from a cracked p-trap and stopped up condensate line. Cut out old, blew out line and piped P-trap back in. System looks good and running great at this time.
Complete: Carrier Split HP: Came to change Condenser coil. There was no refrigerant in the system. Cut out old condenser. Added new One. Pressurized with Nitrogen and pulled vacuum. No leaks. Added 5lbs of 410a Checked charge and system and running great at this time.
Goodman a/c no cooling
Complete: Carrier Split Heat Pump: Found Drain line stopped up. Plywood had hole cut in it for P-Trap. (Pics in Docs) Ptrap condensation was running onto ceiling above dining room table. (Pics in Docs) Cut out P-Trap. Blew out condensate line. Replaced Ptrap and ran new line in secondary pan. (Pics in Docs). Checked charge. System looks good and running great at this time.
FIXED air conditioner
Worked on Goodman split heat pump test system operation did not find any problem system is working properly
Worked on Goodman heat pump system had a clogged drain line clear drain line replace P-trap install secondary float switch for drain pan system running properly
Worked on Goodman split heat pump found leak on evaporator coil ordering new coil returning when part comes in
Replaced customers defective thermostat Cycle System running properly
Worked on Goodman package unit found system low on refrigerant preformed electronic Leak search found system leaking at evaporator coil and accumulator ordering parts returning to repair
Goodman Split heat pump no cooling
Incomplete: 2 Systems: Worked on downstairs Unit: Goodman Package Unit. HO said wasn’t meeting desired temp. At the Package Unit found unit frozen up. (Pics in Docs) told HO of situation and told to leave unit off so it can thaw. Need to reschedule for thaw out.
Work on Carrier heat pump system slightly low on refrigerant added 2 lb system is running properly
Worked on Payne heat pump found system leaking refrigerant from accumulator order new part needs a return when the part comes in
Duct work pulled out duct
Goodman split heat pump no cooling
Worked on Payne heat pump system is working properly came here after previous technician had to let system defrost looks like customer just had a dirty filter system is working great at this time
Goodman split heat pump no cooling