Comfort First is Jackson Springs, NC’s experts in heating, cooling and all-around home comfort.
We’re proud of our Jackson Springs, NC reviews for all of our heating, cooling & comfort services, so come take a look!
for Jackson Springs, NC
Our Reviews by City
Complete: 1 System: York Split HP: HO said was fine for the summer got back four days ago and wasn’t AC wasn’t cooling. I checked charge and was extremely low. Performed leak search. At AH found nothing. Opened top of condenser and could see oil in the bottom and noticed suction line and liquid line rubbing and found leak there. Cut out section of liquid line and repaired and brazed back together. Pressurized with nitrogen and Pulled Vacuum. No leaks. Added 8lbs of r22. Checked Delta T. System looks good and running great at this time.
performed preventive maintenance on Amana heat pump AC
Heating maintenance on Bryant gas furnace
Heating maintenance on heil package heat pump
4 ton heat pump replacement
Preventive maintenance on a heil heat pump