Local Heating & A/C Services in Kill Devil Hills NC
Your house just wouldn’t be a home without the right heating and air conditioning repair services! With Comfort First Heating & Cooling, you can always be certain that your home in the Kill Devil Hills area maintains the perfect temperature. Along with our repairs, maintenance and replacements, we also offer products such as ductless mini splits . Through our actions, we create customers for life.
Your Air Conditioning and Heating Comfort is our Top Priority.
See what your Outer Bank neighbors are saying about our service below or call us locally at (252) 772-9991 to schedule service.
for Kill Devil Hills, NC
Our Reviews by City
Better than expected
ScottV - Kill Devil Hills, NC
One day and all is done with the HVAC replacement. They even had to do some unforeseen modifications which went smooth as well. Manny and Omar were very respectful and got the job done quickly. I would highly recommend them to anyone in need of an upgraded system. Hands down better service than B&M or George and Co. Comfort First is the best HVAC shop in this area.
Great Team that did a Great Job!!!!
Jerry - Kill Devil Hills, NC
The guys were very respectful very knowledgeable and what they were doing and easy to talk. Would hunt 100% refer them to someone else. Great couple of guys to represent your company no complaints at all.
I was 3 weeks without ac. A lot of mistakes were made, but not by Andy Steed.
Jean - Kill Devil Hills, NC
Andy Steed did a great job in getting my ac back in order after 3 weeks without. He stuck with the problem until he found the solution. Can't say enough great things about him. However, the company as a whole fell down on the job and that's why I was without ac for so long. One mistake on top of another.
Great service, very professional
Tricia - Kill Devil Hills, NC
Carl quickly diagnosed what the problem was with our heat pump and repaired it.
Complete two lower heat pumps. Found insulation sucked to the side blower causing a lack of air flow. Removed insulation and tested the system. System is operating properly at this time.
Complete two upstairs heat pump. Found drain line clogged and cleared out. Assessed duct work. System is operating properly at this time.
Complete two systems, downstairs heat pump. Found clogged drain line and cleared it out. System is operating properly at this time.
2.5 ton Split Heat Pump
4 ton Goodman Split Heat Pump
2 ton Split heat pump Goodman
Trane heat pump checked system found compressor not starting due to bad dual run capacitor and replaced and cycled system working at this time
Check unit found drain broke in wall/ electrical issues
Replaced txv on Trane Heatpump ,
Replace blown fuses chemically clean condenser coil system is running properly now
Replaced blower motor on York heat pump
We installed a 3 ton lennox heat pump and air handler with ten kw heat kit
Cleared primary condensate drain
Replaced 30 amp squared D breaker in sub panel. Checked operation. System working at this time.
Working on Rheem split heat pump Replace warranty low pressure switch and defrost board. Test operation and check all pressures and temps. System is working as it should at this time.
Ruud heat pump fpund to be low in refrigerant and added 2 lb R-410
Trane heat pump found compressor pulling high amps due to bad dual run capacitor and replaced and cycled system working at this time
Amana heat pump found bad control board and replace and cycled system working at this time
Arrived to work on split trane heat pump. Found indoor blower issue, caused by a bad fan relay. Replace fan relay and test operation. System working at this time.