Comfort First is Knightdale, NC’s experts in heating, cooling and all-around home comfort.
We’re proud of our Knightdale, NC reviews for all of our heating, cooling & comfort services, so come take a look!
for Knightdale, NC
Our Reviews by City
Dandrea - Knightdale, NC
The people are great and very knowledgeable
Mm - Knightdale, NC
Timika - Knightdale, NC
Shawn was awesome. He explained things perfectly. Out of all the techs we’ve dealt with from your company, he was by far the best!!! He took our frustrations and concerns very seriously!!! Thank you Shawn!!!
Really great job
ERIN - Knightdale, NC
We had our new HVAC installed today by Devin and Josh. They were here early, very professional, and stayed here til late this evening to make sure our new unit was up and running since it was going to be so cold tonight. Can’t say enough how thankful we are for their dedication and would recommend comfort first to anyone because of these two guys specifically. So thankful.
Laurie - Knightdale, NC
Cody and Jeremy were fantastic. They were polite and informative. They explained everything I needed to know about the new system. We had been without heat for a couple of weeks. The first night they started the install was supposed to get in the low 20’s. They modified the install process so we had heat that night. I would definitely recommend their services to anyone in the Raleigh area.
Dave - Knightdale, NC
Ricky and Omar were extremely professional and did a quick, courteous and thorough job. I told them I'd just gotten home from an overnight shift and needed to sleep. They promised to be as quiet as possible while installing a new unit. They were! I got a great sleep and woke up just as they were finishing up. They were very friendly and answered all my questions with a smile. They left everything as clean as it was before they arrived. Given that I was asleep most of the time they were there -- it was almost like a new unit just magically appeared! I'd recommend their work to anyone. Thank you!
Not Rushed, Took the Time to Check Things Out Thoroughly & Completely
Elizabeth - Knightdale, NC
In the past I guess I was used to the "quicky" check up on HVAC... Today I was pleased that John with Comfort First did an excellent job! As I put in the title, he was not rushed, took the time to check things out thoroughly and completely, AND answered questions and explained! He came when scheduled, let us know exactly when he'd arrive, and scheduled also had when WE wanted it scheduled! Thanks!
Michael - Knightdale, NC
Winston - Knightdale, NC
The technician was very courteous.He explained the process of his visit,service call. He diagnosed the problem,corrected it,Thanks!!! Great
Incomplete 1 System Lennox HP Split System. HO stated system was not cooling. Found system extremly low in ref. Performed a leak search. Found leak at the condenser and evap coil. Both parts need to be replaced. Will have to call Lennox to get parts info. Condenser Data: M#: 13HPD-048-230-01. S#: 5806F09461. AH Data: M#: CB26UH-048-230-1. S#: 6006D61087. System holds 14 lbs of R22.
Complete 1 System Goodman Gas Pak Straight A/C: HO stated system was not cooling. Found condenser coil way too dirty. Cleaned it with coil cleaner. Checked charge. Found it low in ref. HO authorized me to add ref. Added 1 lbs of R22. Checked delta t. System was running great. Loss charge due to discharge core valve got stuck. Had to replace discharge core valve. Recharge unit at no charge per Jimmy. Added 2 1/2 lbs of R22. Checked pressures. System is running great at this time.
Carrier split heat pump found bad run capacitor
Goodman ac replace condenser coil
Gmc....ac replaced condenser coil
Goodman air handler checked system found water in secondary drain pan due to craked primmy drain pan need to replace primmy dran pan
Carrier gaspack blown daul capacitor
Complete 1 System 2 zones Lennox Straight A/C: replace blower motor. Checked pressures. system is running great at this time.
Complete 1 Systems worked on Amana Gas Pak Straight A/C. Cooling Maintenance. Checked thermostat and air filter. Checked blower motor amp draw. Checked all wiring. Inpected evap coil. Made sure drain line was clear. Checked cfm and compressor amp draws. Checked all wiring at condenser. Checked dual run cap. Checked pressures. Cleaned condenser coil. System is running great at this time.
Complete 1 System 2 Zones Trane Straight A/C: HO stated when she had tstat on US she would still feel air coming out at the ds vents. Found motor damper miss wire. Rewired. Tested both zones, they are working properly now. Checked pressures. System is running great at this time.
Complete 1 System Goodman Pak HP System. AHS Maintenance. Checked thermostat and air filter. Checked blower motor amp draw. Checked all wiring. Inpected evap coil. Made sure drain line was clear. Checked cfm and compressor amp draws. Checked all wiring at condenser. Checked dual run cap. Checked pressures. Rinsed condenser coil. System is running great at this time.
Goodman package unit
Goodman split heat pump Replaced evaporator coil compressor service valves recharged system ensured system working properly
Goodman split straight a.c. repaired low voltage short
York s9lit heat pump. Checked system for proper operation
Trane split heat pump Replaced faulty discharge air temp sensor with new
Carrier split heat pump Replaced service valves
Trane cooling tune up