Comfort First is Knightdale, NC’s experts in heating, cooling and all-around home comfort.
We’re proud of our Knightdale, NC reviews for all of our heating, cooling & comfort services, so come take a look!
for Knightdale, NC
Our Reviews by City
Not Rushed, Took the Time to Check Things Out Thoroughly & Completely
Elizabeth - Knightdale, NC
In the past I guess I was used to the "quicky" check up on HVAC... Today I was pleased that John with Comfort First did an excellent job! As I put in the title, he was not rushed, took the time to check things out thoroughly and completely, AND answered questions and explained! He came when scheduled, let us know exactly when he'd arrive, and scheduled also had when WE wanted it scheduled! Thanks!
Michael - Knightdale, NC
Winston - Knightdale, NC
The technician was very courteous.He explained the process of his visit,service call. He diagnosed the problem,corrected it,Thanks!!! Great
3 system tune ups, package unit, two straight a.c.. Found two bad dual capacitors.
Two unit cooling maintenance on carrier and trane
2 unit cooling maintenance
Gaspack cooling maintenance
Trane heat pump completed cooling maintenance and found bad dual run capacitor and replaced and cycled system working at this time
Complete: Trane Split HP: Replaced blower motor cycled system a couple times and system is working great at this time.
Repaired a Goodman gas pack by replacing the evaporator coil
Trane air handler checked system found not blowing are due to bad blower motor
Carrier found low voltage short on control wires
Repaired a carrier gas furnace by replacing the pressure switch
Carrier heat pump low-voltage short in outdoor unit
Carrier gas pack.....not heating...idm....blowermotor....bad
Carrier gas furnace no heat blockage drain line pressure switch damaged due to water
Goodman gas package unit. Replaced control board and igniter for furnace
Goodman heat pump. Replaced bad dual capacitor
Lennox gas furnace heating maintenance
Repaired Goodman split system by replacing blower motor assembly with wheel check system cooling at this time
Carrier heat pump. Found faulty heat strips