Comfort First is Knightdale, NC’s experts in heating, cooling and all-around home comfort.
We’re proud of our Knightdale, NC reviews for all of our heating, cooling & comfort services, so come take a look!
for Knightdale, NC
Our Reviews by City
Dave - Knightdale, NC
Ricky and Omar were extremely professional and did a quick, courteous and thorough job. I told them I'd just gotten home from an overnight shift and needed to sleep. They promised to be as quiet as possible while installing a new unit. They were! I got a great sleep and woke up just as they were finishing up. They were very friendly and answered all my questions with a smile. They left everything as clean as it was before they arrived. Given that I was asleep most of the time they were there -- it was almost like a new unit just magically appeared! I'd recommend their work to anyone. Thank you!
Not Rushed, Took the Time to Check Things Out Thoroughly & Completely
Elizabeth - Knightdale, NC
In the past I guess I was used to the "quicky" check up on HVAC... Today I was pleased that John with Comfort First did an excellent job! As I put in the title, he was not rushed, took the time to check things out thoroughly and completely, AND answered questions and explained! He came when scheduled, let us know exactly when he'd arrive, and scheduled also had when WE wanted it scheduled! Thanks!
Michael - Knightdale, NC
Winston - Knightdale, NC
The technician was very courteous.He explained the process of his visit,service call. He diagnosed the problem,corrected it,Thanks!!! Great
Carrier second floor AC low 35 5 dual capacitor
Repaired a Goodman heat pump by replacing the evaporator coil and recharged system
Checked system found water in secondary drain pan due to stopped up primary drain line and cleared and cycled system working at this time
Worked on Goodman 2zone Heat pump system .found low on R410a ,adjusted charge-cleared drain line. Set charge by super heat
Goodman furnace wire loose at disconnect no power
We just installed a 3 ton 14 seer Goodman package unit with an 8kw heat kit
IDP AC checked system found bad dual run capacitor and also found system to be out of refrigerat and preferred leak search and found leaking case coil
Goodman A/C checked system found stopped up primary drain line and cleared and cycled system working at this time
Carrier heat pump checked system found bad condenser fan motor need to replace
Changed fan motor on outdoor unit
Inspected duct work
Goodman gas pack
Found bad condensate pump, safety switch cut off unit.
Found restriction in straight ac
Inspected duct work for issues. No problems, good flow.
Inspecting duct under house for water damage after water pipe began leaking.
Replace Zone damper motor on Carrier equipment
Replace control damper Motor Carrier equipment