Comfort First is Lillington, NC’s experts in heating, cooling and all-around home comfort.
We’re proud of our Lillington, NC reviews for all of our heating, cooling & comfort services, so come take a look!
for Lillington, NC
Our Reviews by City
Great Job by a good company
Kevin - Lillington, NC
Cohen Family - Lillington, NC
Our technicians were prompt, friendly, and did the job! There was more wrong with my system then initially realized but they cared for it. I will highly consider getting the care plan with them for future maintence!
Outstanding service technicians
Mike - Lillington, NC
Jessica - Lillington, NC
Comfort First is the best!!!
Fermin - Lillington, NC
The installers were fast and cleaned up after themselves. Sean was very knowledgeable and very professional. Carlos was the hardest worker I have ever seen. The other guy was a hard worker too. They were amazing! Renee was very knowledgeable and professional. She came out last minute and late at night to take care of my family. Another company was trying to tell me that I HAD to replace both of my systems and I couldn't even get a word in. Completely night and day from their scare tactics and Renees honesty. She said why would I replace a unit that is not broken. Very genuine. I love Comfort First and will be referring them to my friends and family. I was actually referred by my neighbor who just had a system installed by them too!
Lucy - Lillington, NC
She was excellent. Very detailed. Helped answer all questions while also putting up with a screaming child.
Goodman split hp no cooling
Performed system diagnostic on Goodman heat pump
Provided an estimate for a customer to replace their mobile home split heat pump with a package heat pump and full duct placement. We will be installing an Amana 16 seer next week.
Working on trane heat pumps
Working on heil heatpump
Air conditioning repair and maintenance service.
Maintenance on Lennox Split Heat Pump: Air Handler: Checked Amp Draws on the Blower Motor , checked the capacitor and blower wheel. Inspected and cleaned Evap coil. Heat Pump: Checked the charge, and the capacitor. Check the Amp draws on the fan and compressor. Cleaned Unit. System looks good and running Great at this time.
Working on lennox heat pump
Lennox Split Heat Pump: Air Handler: Checked Amp Draws on the Blower Motor and Heat strips, checked the capacitor and blower wheel. Inspected Evap coil. Heat Pump: Checked the charge, and the capacitor. Check the Amp draws on the fan and compressor. Cleaned Unit. System looks good and running Great at this time.
Colling maintenance on a heil heat pump
21419/complete/2 systems/ trane hp splits/ did heating epa on both systems. Checked caps. Amps. Freon. Defrost. Heat kits. Tstats. Washed coils. Found blower motor on down stairs system amping a little high but still doing its job. All is heating and is fine at this time.
Repaired Goodman heat pump by fixing a broke wire
Goodman Split Heat Pump HO said he smelt burning and saw smoke. Went to the Air Handler Found bad motor. Replaced motor and capacitor. System is running great at this time.
Heil Split Heat Pump: Replaced Defrost Board and sensor. Checked the capacitor and it was bad. Changed the capacitor. System is running great at this time.
Working on rheem heatpumps
Diagnosed a bad blower motor and blower board on a heil heat pump
Performing load calc for customer to determine if the system is the correct size.
Working on a Lennox heat pump
Trane Gas Pack: Homeowner said Heat was blowing into one room and none of the others. Checked the vents in the rooms the gas pack covered in the main floor. Heat was only getting to the Master bedroom. There were no more vents blowing in the other rooms. Went to the unit and it was working fine. Checked capacitors and amp draws. Found one bad capacitor. Replaced it and the unit fired back up. The Gas Pack is operating as it should. Checked the air flow once more and it was working great.
Heating maintenance on 2 Goodman heat pumps
Goodman Split Heat Pump: Worked on upstairs Unit. HO said the unit wasn’t coming on. Checked power to the unit all was good. Checked thermostat wires found two shorts (red to thermostat, yellow to heat pump) which also lead to a bad thermostat.. Replaced the thermostat. Found bad sequencer, Replaced it. Went outside unit found a bad contactor, replaced it. Unit is working great at this time.
Goodman split HP no heat:
2 Lennox Split System Heat Pumps: EPA Maintenance on both.Upstairs Unit Heat Pump: Checked Amp draws on fan motor and compressor. Checked Capacitor. Checked charge. And cleaned the system. Air handler: Checked Amp draws on blower motor and heat strips. And cleaned the system.Downstairs Unit Heat Pump: Checked Amp draws on fan motor and compressor. Checked Capacitor. Checked charge. And cleaned the system. Air handler: Checked Amp draws on blower motor and heat strips. And cleaned the system.
Goodman split heat pump. Replaced heat strips in the furnace. After connecting the heat strips the unit still didn’t kick in the strips. Checked the board found burnt wire in the board and replaced with an ICM277c board. Once installed the unit fired up. Cycled the unit from the upstairs and downstairs thermostats twice. Started and shut off perfectly.