Comfort First is Linden, NC’s experts in heating, cooling and all-around home comfort.
We’re proud of our Linden, NC reviews for all of our heating, cooling & comfort services, so come take a look!
for Linden, NC
Our Reviews by City
Taitague - Linden, NC
Peyton and his crew came early and were very courteous and professional.
Doris - Linden, NC
Elmer - Linden, NC
I would like to say Ms.Renee McFadden is an out standing representative for Comfort First heating and cooling. She is very well informed and helped me understand what is going on with my heat pump. Again Thank you for the great service and information. Thank you are your business...
replaced capacitor on Payne heat pump AC split system
repaired drain line on Goodman heat pump AC split system
added r22 refrigerant to Goodman heat pump AC split system
Goodman split heat pump maintaince
Complete: 2 Systems: Worked on Upstairs Unit: Goodman Split HP: Came to replace accumulator. Recovered old refrigerant. Unable to remove old filter dryer due to location inside of unit. Did add new filter dryer to liquid line. Removed old accumulator and installed new. Pulled vacuum and recharged system with 9lbs of 410 refrigerant. Informed HO that both units need cleaning. She said that her husband was deployed and he would have to make that decision for Maintenance. System looks ok and running great at this time.
Goodman split heat pump no cooling
Left Side if House: Amana Split Heat Pump: Air Handler: Checked Thermostat and Capacitor, Filters and Amp Draws on the Blower Motor, Inspected Evap coil. Replaced P-Trap, checked condensate line. Heat Pump: Checked the charge, and the capacitor. Check the Amp draws on the fan and compressor. Cleaned Unit. Washed Coils System looks good and running Great at this time.
Carrier split ac. Replaced leaking case coil and recharged system
Goodman split heat pump. Found faulty condensation pump causing unit to not run. Installed new condensation pump and ensured proper operation of unit
Cooling maintenance on 2 heil heat pumps
Working on carrier heatpump
Working on heil heatpump
Routine maintenance on a heil heat pump
Just finished installing a 3.5 ton 16 Seer Amana Split heat Pump and a Google Nest Thermostat.
Heating maintenance on a Goodman heat pump
Providing an estimate for a customer to replace their split heat pump
Heating maintenance on 3 Bryant heat pumps
Working on goodman heat pump.
Cooling maintenance on rheem gaspack
Providing customer with an estimate to replace duct work previously installed incorrectly by another contractor.
Leak search on rheem package unit.
Replaced outdoor fan motor on split heat pump ac system
Goodman heat pump not cooling
Goodman package heat pump not cooling