Comfort First is Linden, NC’s experts in heating, cooling and all-around home comfort.
We’re proud of our Linden, NC reviews for all of our heating, cooling & comfort services, so come take a look!
for Linden, NC
Our Reviews by City
George - Linden, NC
Juan was excellent and a great representative for the company. He was thorough, competent and professional. He kept us in the loop throughout the process and we would recommend him to anyone in need of his skills set.
Awesome job explaining the different options available.
Leisa - Linden, NC
Renee did an awesome job explaining the different options, and the different types required vs recommended items, such as size, duct work, etc. I was very pleased with the outcome.
Taitague - Linden, NC
Peyton and his crew came early and were very courteous and professional.
Doris - Linden, NC
Elmer - Linden, NC
I would like to say Ms.Renee McFadden is an out standing representative for Comfort First heating and cooling. She is very well informed and helped me understand what is going on with my heat pump. Again Thank you for the great service and information. Thank you are your business...
Routine maintenance on 2 Goodman heat pumps
Complete one system, Carrier split heat pump, 3 zones. Preformed heating maintenance and found no issues with the system. System is operating properly at this time.
Complete: 1 System: HSA Maintenance Heil Split Heat Pump: Air Handler: Checked Thermostat and Capacitor, Filters and Amp Draws on the Blower Motor, Inspected Evap coil. Inspected Ptrap and checked condensate line. Heat Pump: Checked the charge, and the capacitor. Check the Amp draws on the fan and compressor. Washed Coils System looks good and running Great at this time. $0 Collected
Notes added by tech BJ McLeod 168 on 9/24/2020 12:33:35 PM Complete Goodman Split Heat Pump Customer complained that the blower motor was operating nonstop. Replaced the circuit board at the AHU due to a defective blower relays on the board.
Complete 2 systems, upper Goodman heat pump split. Found bad dual capacitor and replaced. System is operating properly at this time.
Complete one system. Found burnt wire in capacitor and replaced. System operating properly at this time.
added r22 refrigerant to Rheem gas pack
Rheem split heat heat pump no cooling
Rheem split heat pump no cooling
1 unit AHS maintenance,Hiel Zone System added 2 pounds of r22 refrigerant
1 unit maintenance Heil Zone system Added R22 freon
Westinghouse ac check
Rheem ac check
Trane split Heat pump cooling maintenance
Heil split heat pump no cooling
3.5 ruud heat pump
4 ton Amana heat pump and duct system
Completed cooling maintenance on heil split heat pump
Found leaking evap coil on cattier split heat pump
Goodman package unit Heat pump cooling maintenance
Completed cooling maintenance on two amana split heat pumps
Incomplete: 2 systems Carrier Split Heat Pumps worked on both systems. US Unit: HO said was blowing hot air in cool mode. Checked charge and it was fine. Reversed refrigerant flow and it was good. Checked amp draws on all including heat strips and all all seemed to be working as it should. DS Unit: TN said that unit would cycle on and off quickly. Found system completely out of refrigerant. Performed leak search and found system leaking at Evap coil. Checked the rest of system out and the only place I was getting reading was at the AH. Need a new Evap coil.
Ruud split system Heat Pump