Mint Hill, NC depends on Comfort First for heating, cooling and comfort needs.
Read our Mint Hill, NC reviews below to see how we always go beyond the call of duty.
for Mint Hill, NC
Our Reviews by City
Kelly - Mint Hill, NC
Top notch knowledge
Dominique - Mint Hill, NC
Billy has an ability that most technicians don’t. He has the ability to share is knowledge of HVAC and explain how things work and don’t. We appreciate his service!
Billy gave great service
Reanna - Mint Hill, NC
Brad Was Great!
Coley - Mint Hill, NC
He was excellent. He was knowledgeable and very efficient. We appreciate him.
Great and quick
Scott - Mint Hill, NC
Etawn - Mint Hill, NC
Excellent Customer Service
Great customer service
Robert - Mint Hill, NC
Billy was quite efficient and personable. He quickly identified the problem and got me set up to have the issue fixed.
Great service and Great price
Vivian - Mint Hill, NC
Billy was very professional and did a great job.
Kevin - Mint Hill, NC
Jeremy - Mint Hill, NC
It was great.
Great and trustworthy service
Jack - Mint Hill, NC
Great service. Very personable and trustworthy tech. His name was Billy
Very good service, tech was on time and did a thorough check of my heating unit.
Alberta - Mint Hill, NC
Fast, responsive, courteous service
Amanda - Mint Hill, NC
Wonderful customer service, thorough
Wendy - Mint Hill, NC
They came out to the house because I had no heat. They replaced the thermostat and the heat still wasn’t working. They came back out and discovered the blower motor was bad. They replaced it in no time and had me warm and toasty again!! Thank you Billy and Cody, you’re the best!
Ben - Mint Hill, NC
Billy and cody were both very professional, knowledgeable and answered all my questions thouroughly.
Jones - Mint Hill, NC
Terry was great on has my heat pump running great
Holly - Mint Hill, NC
Michael was wonderful. very knowledgeable and explained everything to me. also offered great advice on maintaining my HVAC equipment. great service thanks Michael.
Complete two systems. Worked on upstairs system. Found low in refrigerant and added 1lb of r22. System is operating properly at this time.
Complete one system, main. Found no issues with duct work. Found system low in refrigerant and added 1 lbs of r410a. System is operating properly at this time.
Ac unit not working
Completed two systems, worked on both upstairs and downstairs. Upstairs system, found 35/5 mfd capacitor failed open and replaced. Cleaned condenser coil. Downstairs system, Trane ac split, found dirty condenser coil and cleaned. System operating properly at this time.
Co pressor replacement
Worked on Goodman gas furnace
Work on gas furnace
Compressor on heat pump locked up.
Worked on Lennox gas furnace
Carrier heat pump
No heat and heat maintenance and fixing inducer draft motor
Work on Carrier gas furnace
Worked on Lennox gas furnace
Worked on Carrier gas furnace
Worked on Trane air conditioner
Worked on Carrier Air Conditioner
Worked on Lennox air conditioner
Worked on air conditioner
Goodman gas pack with burnt inducer motor
Goodman gas furnace had to clean out drain lines with nitrogen and glue drain together also add event to the top of the Trap
Worked on Comfortmaker air conditioner
Worked on a Trane air conditioner