Comfort First is Morrisville, NC’s experts in heating, air conditioning repair and all-around home comfort.
We’re proud of our Morrisville, NC reviews for all of our heating, cooling & comfort services. See what your neighbors are saying below!
To have your AC repair in Mooresville, you’ll most likely be paying in the range of $161 – $548. As you probably already know, the amount is going to vary significantly by what type of repair you need, what system you own and what AC repair company you choose in Mooresville. Some companies such as Comfort First Heating & Cooling offer specials and financing options to make what you pay easier and as low as possible.
Get your quote from Comfort First today!
How much it costs to replace your air conditioning unit in Mooresville, NC depends on:
- What type of system you are interested in. A high-end system can cost you $12,000 while a more modest one can cost around $900.
- Which company you choose and what their financing and specials options are. You’ll need to tack on a little more to include labor costs and of course subtract any great AC deals.
Give Comfort First Heating & Cooling a call for a more precise idea about what you can expect to pay locally for an AC replacement.
AC maintenance once a year will keep your system in top shape. Signing up for an HVAC maintenance plan will allow you to put your cooling concerns on the back burner while ensuring your system is taken care of by an AC expert.
Make sure that expert is a trusted professional by choosing Comfort First Heating & Cooling for all of your AC needs. Contact us today.
for Morrisville, NC
Our Reviews by City
AC install Comfort Air
Ramasaran - Morrisville, NC
Bkarki - Morrisville, NC
why copper tubing cast was tagged on, that should have been part ob the install equipment process/work order. But for Soldering the copper tubes No modifications were done.
Workers were very polite and professional
Coker - Morrisville, NC
Tempstar gas furnace and Amanna gas pack completed EPA heating maintenance and cycled system working at this time
Complete 1 System 3 Zones Lennox Straight A/C: Came to replace motor damper for 3rd Floor. Tested it. System is properly working.
Carrier gas furnace found bad cfm
Lennox gas furnace found bad capacitor
Rheem gas pack checked system found compressor not starting due to bad dual run capacitor and replaced with truck stock capacitor and cycled system working at this time
Carrier A/C completed cooling maintenance and cycled system working at this time
Lennox A/C checked system found bad zone damper motor need ro replace zone damper motor
Trane Heat pump replaced indoor 5XV and bi flow drier and cycled system working at this time
Complete 2 Systems worked on US Carrier Straight A/C: replaced case coil. Recovered ref. Removed old case coil. Installed new one in. Replaced p trap, and made sure drain line was clear. Leak tested system. Pulled vacuum. Added 9 lbs of 410A. Checked pressures. System is running great at this time.
Amana gas pack performed cooling maintenance
Lennox equipment noise
Complete 2 Systems worked on US Carrier Straight A/C: HO stated system was not cooling. Found system low in ref. Added 2 lbs of 410A. Added a can of leak stop. System is running great at this time.
Complete 2 Systems worked on DS Goodman A/C: HO said system ds was not cooling. Found way too dirty air filter. Removed it. HO getting new one later on. Found a burnt wire at condenser, the common wire going from contactor to dual cap common side. Repired wire. Checked pressures. System is running great at this time.
Lennox ac check
Goodman gas furnace performed cooling maintenance
Complete 1 System worked on Lennox HP Split System: Cooling Maintenance. Checked thermostat and air filters. Replaced Air filter provided by HO. Checked blower motor amp draw. Checked all wiring. Inpected evap coil. Made sure drain line was clear. Checked cfm and compressor amp draws. Checked all wiring at condenser. Checked dual run cap. Checked pressures. Cleaned condenser coil. System is running great at this time.
Rheem ac check
Lennox bad compressor