Comfort First is Morrisville, NC’s experts in heating, air conditioning repair and all-around home comfort.
We’re proud of our Morrisville, NC reviews for all of our heating, cooling & comfort services. See what your neighbors are saying below!
To have your AC repair in Mooresville, you’ll most likely be paying in the range of $161 – $548. As you probably already know, the amount is going to vary significantly by what type of repair you need, what system you own and what AC repair company you choose in Mooresville. Some companies such as Comfort First Heating & Cooling offer specials and financing options to make what you pay easier and as low as possible.
Get your quote from Comfort First today!
How much it costs to replace your air conditioning unit in Mooresville, NC depends on:
- What type of system you are interested in. A high-end system can cost you $12,000 while a more modest one can cost around $900.
- Which company you choose and what their financing and specials options are. You’ll need to tack on a little more to include labor costs and of course subtract any great AC deals.
Give Comfort First Heating & Cooling a call for a more precise idea about what you can expect to pay locally for an AC replacement.
AC maintenance once a year will keep your system in top shape. Signing up for an HVAC maintenance plan will allow you to put your cooling concerns on the back burner while ensuring your system is taken care of by an AC expert.
Make sure that expert is a trusted professional by choosing Comfort First Heating & Cooling for all of your AC needs. Contact us today.
for Morrisville, NC
Our Reviews by City
AC install Comfort Air
Ramasaran - Morrisville, NC
Bkarki - Morrisville, NC
why copper tubing cast was tagged on, that should have been part ob the install equipment process/work order. But for Soldering the copper tubes No modifications were done.
Workers were very polite and professional
Coker - Morrisville, NC
Amana gas pack performed cooling maintenance
Lennox equipment noise
Complete 2 Systems worked on US Carrier Straight A/C: HO stated system was not cooling. Found system low in ref. Added 2 lbs of 410A. Added a can of leak stop. System is running great at this time.
Complete 2 Systems worked on DS Goodman A/C: HO said system ds was not cooling. Found way too dirty air filter. Removed it. HO getting new one later on. Found a burnt wire at condenser, the common wire going from contactor to dual cap common side. Repired wire. Checked pressures. System is running great at this time.
Lennox ac check
Goodman gas furnace performed cooling maintenance
Complete 1 System worked on Lennox HP Split System: Cooling Maintenance. Checked thermostat and air filters. Replaced Air filter provided by HO. Checked blower motor amp draw. Checked all wiring. Inpected evap coil. Made sure drain line was clear. Checked cfm and compressor amp draws. Checked all wiring at condenser. Checked dual run cap. Checked pressures. Cleaned condenser coil. System is running great at this time.
Rheem ac check
Lennox bad compressor
Goodman gas pack and /C completed cooling maintenance
Lennox air handler replaced zone damper motor and cycled system working at this time
Goodman A/C reclaimed refrigerate replaced compressor bi flow drier and recharged system with 9 lb R438A and cycled system working at this time
Working on a Goodman heat pump
Working on 2 Lennox heat pumps
Lennox gas furnace found bad ECM replaced 1075 hp 1/3
Goodman ac check
Lennox ac check
Amana ac check
Lennox ac.....intermittent air to second floor
Amana ac.....cooling maintenance