Comfort First is Pinehurst, NC’s experts in heating, cooling and all-around home comfort.
We’re proud of our Pinehurst, NC reviews for all of our heating, cooling & comfort services, so come take a look!
for Pinehurst, NC
Our Reviews by City
Thorough, patient, knowledgeable installer.
Teresa - Pinehurst, NC
I am not tech savvy so I hesitated getting the Nest products. The installer BJ was very patient in answering my questions and explained things in terms that were easy for me to understand.
Degrange - Pinehurst, NC
The service was quick and efficient. Our technician was knowledgable, thorough and personable. We are very pleased with the service and will definitely use Comfort First again as well as recommend them to our friends.
Great service Andy is the best
Malloy - Pinehurst, NC
Paul - Pinehurst, NC
Fixed problem called out for and found another problem he addressed as well.
Great once again!
Adams - Pinehurst, NC
Friendly, knowledgeable, and skilled.
B.J. was courteous, knowledgeable, approachable about questions and delivered the info we needed!
Sally Adams - Pinehurst, NC
As I said above, B.J. was a great representation of your company, thoroughly and knowledgeably checked what our concerns were and delivered helpful suggestions.
Dale - Pinehurst, NC
Good guys, Comfort lucky to have them
John - Pinehurst, NC
BJ was our technician and a pleasure to work with. He explained each issue, sympathized with our situation, and offered helpful information. We would definitely recommend Comfort First.
Nicholas - Pinehurst, NC
Fast, Professional, Polite
Righting a wrong
Susan - Pinehurst, NC
I am so thankful to service manager, Jimmy Pierce, and expert service technician, David Miles for righting a wrong by a former technician. I was heard, as an upset customer, and immediately took care of my situation and got my heat flowing again.
Routine maintenance on 3 Amana heat pump systems
2 system maintenance on Trane heat pumps
Routine maintenance on a Goodman heat pump and a Lennox heat pump
Replacing a thermostat for a Trane heat pump
Routine maintenance on a Carrier heat pump
Checking 2 Trane heat pumps
Routine maintenance on a Trane heat pump
Working on an American Standard dual fuel split system
Replaced a capacitor on a Trane heat pump
Replaced a thermostat on a Trane heat pump
Replaced a capacitor on a Trane heat pump
Working on a Carrier heat pump
Cleaning and repiping a drain line on a Bryant air handler
Serviced and clean 3 systems -found six.heaters bad-repaired-operation good 🙂
Complete: Installed Nest IQ camera, doorbell, door lock and Tstat. Got customer all set up via the app and how to work everything. All looks good and running great at this time.
Found bad capacitor on 1st floor and drain line backed up on 2nd floor-cleared drain .operation good at this time
Performed EPA on carrier/Bryant system
Check trane heat pump -found bad defrost board
Found evap coil leaking on Goodman heat pump system-performed leak search-
Work on York Heat Pump.found shorted high voltage wire due to loose connection,flushed drain line.
Replaced txv on a Heil heat pump
Check ductwork-repaired missing insulation around boots
Replaced condensate pump on carrier system ,
Complete: 3 Systems worked on Main Area Unit: Carrier Split HP: homeowner concerned not cooling as well since they installed a new generator. The power was cut off for a while and when it came back on it didn’t seem to be acting just right. Checked the charge and her temperature split and it was perfect. The thermostat was satisfied and she was basing the temperature on her feeling. The thermostat had a program on it that must have reset to default when the power was cut out. Was an old carrier programmable thermostat. Showed her how to change the program. Told her about the nest thermostats and gave her some information about them. At this time the system looks good and running as it should. Also the homeowner would like for us to set up a time to come and look at her upstairs ductwork. Seems to have poor airflow on one side and bad condensation on the other side.
Worked on Trane Heat pump-found bad capacitor-repaired operation good at this time-customer Interested In maintenances agreement