Trust Comfrot First when it comes to heating, cooling and the full comfort picture in Pittsboro, NC.
To see how we combine great customer service with professional heating and cooling services in Pittsboro, NC, check out our reviews.
for Pittsboro, NC
Our Reviews by City
New A/C install
Alonzo - Pittsboro, NC
Great Customer Service
Micah - Pittsboro, NC
Cody did a great job of explaining everything in detail as to what was wrong with my HVAC system and even answered several texts to help me identify issues after hours. Overall, I rate his customer service 5 stars!
Hudson - Pittsboro, NC
Very friendly, good at explaining technical terms, cared about saving us money and not doing any services that weren't necessary.
Eric - Pittsboro, NC
Tony was prompt, courteous, and respectful. He quickly diagnosed the problem and replaced a blown transformer. Hi was both professional and friendly.
Barbara - Pittsboro, NC
Heat Pump Install
Mr Jones - Pittsboro, NC
Heat Pump Install
Mr - Pittsboro, NC
Sean and Carlos were very professional and respectful of the property. Unit was installed and operational by midday.
Awesome customer service experience!!!
John S - Pittsboro, NC
Thanks to Margaret, Jimmy, and the whole service team for one of the best customer service experiences that I've ever had!
Armstrong air handler second-floor evap coil leak
Replace compressor...Goodman gas pack
Goodman package heat pump checked system found condenser fan motor not running due to bad dual run capacitor and replaced and cycled system working at this time
Trane heat pump checked system found bad dual run capacitor and to be low in refrigerant and added 2 lb R-22 to system and cycled system working at this time
Trane package unit blown 40/5 dual capacitor
Rheem HP set Subcooliing and super heat
Lennox A/C bad capacitor
Bryant A/C low in refrigerant R22
Goodman gas apck checked system found high suction pressure and low head pressure due to compressor not pumping to full capacity due to being bad need to replace compressor
Found water in secondary drain pan due to stopped primary drain line and cleared and cycled system working at this time
Carrier ac checked system found grounded compressor need to replace compressor
Goodman package heat pump replaced blower motor and cycled system working at this time
Weatherking gas pack replaced evap coil and recharged system with 7 lb R-22 and cycled system working at this time
Goodman ac add refrigerant
Goodman ac replace compressor
Amana hp,blower motor
Honeywell dehumidifier checked system found to be out of refrigerat and preferred leak search and found leaking evap coil
Trane mini split clear drain
Amanna heat pump checked system found bad dual run capacitor and replaced and cycled system working at this time
Repaired atrane heat pump by recharging the engine to the correct charge
Coleman AC replace contactor outdoor unit
We installed a 3 ton rheem straight AC and coil with t6 tstat
Trane AC 1bl low r22
Rheem gas Pack 1 lb low R22