Trust Comfrot First when it comes to heating, cooling and the full comfort picture in Pittsboro, NC.
To see how we combine great customer service with professional heating and cooling services in Pittsboro, NC, check out our reviews.
for Pittsboro, NC
Our Reviews by City
New A/C install
Alonzo - Pittsboro, NC
Great Customer Service
Micah - Pittsboro, NC
Cody did a great job of explaining everything in detail as to what was wrong with my HVAC system and even answered several texts to help me identify issues after hours. Overall, I rate his customer service 5 stars!
Hudson - Pittsboro, NC
Very friendly, good at explaining technical terms, cared about saving us money and not doing any services that weren't necessary.
Eric - Pittsboro, NC
Tony was prompt, courteous, and respectful. He quickly diagnosed the problem and replaced a blown transformer. Hi was both professional and friendly.
Barbara - Pittsboro, NC
Heat Pump Install
Mr Jones - Pittsboro, NC
Heat Pump Install
Mr - Pittsboro, NC
Sean and Carlos were very professional and respectful of the property. Unit was installed and operational by midday.
Awesome customer service experience!!!
John S - Pittsboro, NC
Thanks to Margaret, Jimmy, and the whole service team for one of the best customer service experiences that I've ever had!
Goodman split heat pump heating maintenance
Amana gas package unit heating maintenance
Ruud gas package unit. Inspected system to ensure proper operation
Carrier Furnace AC just rechecking system operation
Goodman ac....1bl low
Amana equipment Bad Nest Thermostat
Trane straight a.c.. Diagnosed grounded Compressor
Goodman gas Pack. Diagnosed unit out of refrigerant. Preformed leak search and replaced leaking filter drier. Recharged system and ensured proper operation
Trane split heat pump Diagnosed bad dual cap. Repaired and ensured proper operation
Amana split heat pump heating maintenance
Carrier equipment insufficient cooling
Replace blower motor module carrier package unit
Heating maintenance on a Goodman gas furnace
Diagnosed a bad blower motor module on a carrier gas pack
Diagnosed a leaking condenser coil on a Goodman gas pack
Carrier Control board replacement
Carrier board replacement
Carrier gas pack compressor
Amana AC intermittent cooling at this time
York Furnace heat check
Armstrong air handler second-floor evap coil leak
Replace compressor...Goodman gas pack
Goodman package heat pump checked system found condenser fan motor not running due to bad dual run capacitor and replaced and cycled system working at this time
Trane heat pump checked system found bad dual run capacitor and to be low in refrigerant and added 2 lb R-22 to system and cycled system working at this time