Trust Comfrot First when it comes to heating, cooling and the full comfort picture in Raeford, NC.
To see how we combine great customer service with professional heating and cooling services in Raeford, NC, check out our reviews.
for Raeford, NC
Our Reviews by City
Joseph - Raeford, NC
Bradley did an amazing job. This is the second time I’ve had my HVAC inspected and this time by your business. He was able to quickly identify a leak in the coil and provide information. He was very upfront with timelines and cost for the repair to ease any concerns.
Figgs - Raeford, NC
Not so great at all. Although the technician was very friendly. The receptionist was rude on the phone.
Mccray - Raeford, NC
I’d recommend them if they did a good job.
Ed - Raeford, NC
Service wasn't the best
Fisher - Raeford, NC
All other technicians would put covering on their feet before entering my home. This technician did not. He asked about the thermostat and lowered my temperature. Did not return it back to original temperature I had it set on. The technician also left the light on under our house and we didn't notice it until Sunday, so the light was on for several (5) days.
Great professional and friendly service, great price, thanks.
Darryl - Raeford, NC
I was referred to your company by a coworker and so far I pleasantly pleased with the courteous and honest service my wife and I have received. Beth and Renee have been a pleasure to work with.
Great Service Awesome Technician
Zubida - Raeford, NC
Great Service Friendly Technicians
Great service with competitive prices
Troy - Raeford, NC
Nice, courteous staff
Rashad - Raeford, NC
An Outstanding Service Provider with an attention to the details!
Warrior644 - Raeford, NC
We would definitely recommend Dennis to others; a top-notch HVAC technician! Thanks!
replaced capacitor and defrost sensor on carrier heat pump AC split system
replaced blower control board on Goodman heat pump AC split system
performed diagnostic on carrier heat pump AC split system zoned
found compressor faulty on Goodman heat pump AC split system
performed diagnostic on carrier heat pump AC split system
performed leak search on heil heat pump AC split system
performed heating maintenance on Amana heat pump AC split system.
replaced capacitor on carrier heat pump AC split system
Complete: 1 System. Amana Split HP: Helped complete change out. Wired system, set up nest Tstats and started system. All looks good and working great at this time.
Help complete Change out of new Amana heat pump.
performed diagnostic on Goodman heat pump AC split system air handler
InComplete: 2 systems worked on US system. HO said was blowing out Heat in cool mode. First of all they had the units labeled wrong outside. Both were running and I went by the label instead of double checking the system to see which was US and DS so I spend 30 min working from US AH to DS HP frustrating. When I got it rt the wiring to DS was not getting enough common 24v through contactor to energize reversing valve. Changed contactor. Secondly found Nest Tstat bad. Informed HO that AHS would not cover replacement of a nest and I could put a Tstat on the wall for 137.00 ...... he said he would go get a new nest and put it up himself. It sure if he believed it was a Tstat issue so u told him it would be a recall if he put it up and still didn’t work but if it was still a nest issue that he would be denied and have to pay. System not working correctly at this time.
Estimate for replacing heat pump system
Goodman repaired main drain
Goodman heat pump checked system found water in secondary drain pan due to stopped up primary drain line and cleared and cycled system working at this time
Goodman heat pump checked system found to be frozzen up need to reschedule when system has deiced
replaced contactor on Goodman heat pump AC split system.
replaced capacitor on Goodman heat pump AC split system
replaced condenser fan motor on Kenmore heat pump AC split system
Working on a Heil heat pump
Working on a Ruud heat pump
Replaced heat kit on a Goodman heat pump
Working on a Goodman heat pump
Working on a Heil heat pump
Replacing 2 Amana heat pumps- ainspectwd job