Trust Comfrot First when it comes to heating, cooling and the full comfort picture in Raeford, NC.
To see how we combine great customer service with professional heating and cooling services in Raeford, NC, check out our reviews.
for Raeford, NC
Our Reviews by City
Not so great at all. Although the technician was very friendly. The receptionist was rude on the phone.
Mccray - Raeford, NC
I’d recommend them if they did a good job.
Ed - Raeford, NC
Service wasn't the best
Fisher - Raeford, NC
All other technicians would put covering on their feet before entering my home. This technician did not. He asked about the thermostat and lowered my temperature. Did not return it back to original temperature I had it set on. The technician also left the light on under our house and we didn't notice it until Sunday, so the light was on for several (5) days.
Great professional and friendly service, great price, thanks.
Darryl - Raeford, NC
I was referred to your company by a coworker and so far I pleasantly pleased with the courteous and honest service my wife and I have received. Beth and Renee have been a pleasure to work with.
Great Service Awesome Technician
Zubida - Raeford, NC
Great Service Friendly Technicians
Great service with competitive prices
Troy - Raeford, NC
Nice, courteous staff
Rashad - Raeford, NC
An Outstanding Service Provider with an attention to the details!
Warrior644 - Raeford, NC
We would definitely recommend Dennis to others; a top-notch HVAC technician!Thanks!
Figgs - Raeford, NC
Gary - Raeford, NC
Jon was very knowledgeable and courteous during the service call.
Worked on Goodman heat pump replace common wire Cycle System running properly
Incomplete: two systems: worked on upstairs system: Goodman, split heat pump. Found breaker tripped on outside unit. HO said he tried to flip it back on and immediately flipped off. At the heat pump checked capacitor and it was low, checked to see if there was refrigerant in the system and there was. At the compressor terminals compressor ohmed out on all 3 terminals. Compressor grounded. Informed HO of findings. He said he wanted to order part of it was available. Called Baker. Part on Order.
Worked on Goodman heat pump need to return with new condensing fan motor blade
Complete main level Goodman split heat pump replaced defective condensate pump remove water from secondary pan Cycle System running properly
Worked on Carrier heat pump replace compressor replaced filter drier replaced 45 + 5 microfarad capacitor added 8 lb refrigerant Cycle System running properly
replaced x13 blower motor on Payne heat pump AC split system
clean drain line and replaced pan switch on carrier heat pump AC split system zoned
performed diagnostic on trane heat pump AC split system zoned
added r410a refrigerant to heil heat pump AC split system.
performed leak search on Goodman heat pump AC split system.
adjusted air flow on 2 zone heat pump AC split system zoned
Found blown compressor order new compressor returning when it comes in
Worked on two systems replaced thermostat downstairs and capacitor made low voltage wire repair for upstairs both systems running properly
Clear drain line replace P-trap system running properly
performed diagnostic on Goodman heat pump AC split system
add refrigerant to carrier heat pump AC split system.
Worked on Goodman heat pump did not find any problems with system
Installing new amana split heat pump heating and air conditioning system
Worked on Payne heat pump replace 35 + 5 microfarad capacitor on heat pump ordering new blower motor for air handler
Worked on Payne split heat pump replaced 35 + 5 microfarad capacitor on heat pump order a new blower motor for air handler
performed diagnostic on Payne heat pump AC pack
replaced condensate pump on Goodman heat pump AC split system wall unit
replaced condenser fan motor on Goodman heat pump AC split system.
found x13 blower motor faulty on Bryant heat pump AC split system
performed diagnostic on carrier heat pump AC split system.