Trust Comfrot First when it comes to heating, cooling and the full comfort picture in Raeford, NC.
To see how we combine great customer service with professional heating and cooling services in Raeford, NC, check out our reviews.
for Raeford, NC
Our Reviews by City
Figgs - Raeford, NC
Not so great at all. Although the technician was very friendly. The receptionist was rude on the phone.
Mccray - Raeford, NC
I’d recommend them if they did a good job.
Ed - Raeford, NC
Service wasn't the best
Fisher - Raeford, NC
All other technicians would put covering on their feet before entering my home. This technician did not. He asked about the thermostat and lowered my temperature. Did not return it back to original temperature I had it set on. The technician also left the light on under our house and we didn't notice it until Sunday, so the light was on for several (5) days.
Great professional and friendly service, great price, thanks.
Darryl - Raeford, NC
I was referred to your company by a coworker and so far I pleasantly pleased with the courteous and honest service my wife and I have received. Beth and Renee have been a pleasure to work with.
Great Service Awesome Technician
Zubida - Raeford, NC
Great Service Friendly Technicians
Great service with competitive prices
Troy - Raeford, NC
Nice, courteous staff
Rashad - Raeford, NC
An Outstanding Service Provider with an attention to the details!
Warrior644 - Raeford, NC
We would definitely recommend Dennis to others; a top-notch HVAC technician!Thanks!
Figgs - Raeford, NC
performed diagnostic on York gas pack heating side.
performed diagnostic on Payne heat pump pack
replaced defrost control board on carrier heat pump AC split system
repaired thermostat wire on Goodman heat pump AC split system
Complete: 2 Systems: Worked on Upstairs unit: Goodman Split HP: Unit had no power to the Tstat. Checked AH in wall. Stopped up condensate line and float tripped. Also found bad capacitor. Blew out condensate line. Drained water from pan and changed capacitor. System came on and had a 20 Delta T. System looks good and running great at this time.
Complete: 2 Systems worked on downstairs Unit: Goodman split HP: Added 2lbs of 410a, can of leak stop and Blower cap. Checked charge it was good and Delta T was at 19°. System looks good and running great at this time. Turned Tstat back off and placed key back in lockbox and locked door.
Worked on Goodman heat pump check system operation refrigerant pressures and temperature differential did not find any problems at this time
Worked on Goodman heat pump customers residence had power surge replaced blower control board defrost control board and thermostat Cycle System running properly
Worked on Goodman heat pump for the downstairs replace evaporator coil recharge System test operation running properly
Worked on Trane heat pump for upstairs down broken drain line need to order new pan and return
Working on 2 Payne heat pumps
replaced capacitor on carrier heat pump AC split system
replaced blower control board and added r22 refrigerant to Goodman heat pump AC split system.
performed heating and cooling maintenance on Goodman heat pump AC split system
traced out low voltage short on ICP air handler heat pump AC split system.
reset breaker on Goodman heat pump AC split system air handler
performed diagnostic on rheem heat pump AC split system
cleared drain line on Goodman heat pump AC split system and replaced pan switch
Worked on Goodman heat pump for upstairs added 2 LBS refrigerant hard start kit and leak seal
Worked on Goodman heat pump for the upstairs replace P-trap Cycle System running properly no problems found
Routine maintenance on 2 Goodman heat pumps
Routine maintenance on a Ruud heat pump
Routine Maintenance on an Amana heat pump
Working on a Goodman heat pump
Provided an estimate to replace a split heat pump. Customer decided on a 16 seer Amana. We will be installing next week.