Trust Comfort First when it comes to heating, cooling and the full comfort picture in Raeford, NC.
To see how we combine great customer service with professional heating and cooling services in Raeford, NC, check out our reviews.
On average Raeford homeowners can expect to pay around $500 – $3,500 to have a whole home generator professionally installed. This price is just a reflection of the installation costs, not of the generator itself. It is highly recommended that you have a whole home generator professionally installed. The risks of improper installation include
- Back-feeding the grid.
- Damaging the generator.
- Wiring it incorrectly.
- Failing inspection.
If you air conditioning is not cooling your home in Raeford, there are a few things you can check before calling a technician:
- Is the thermostat set to ON? If so, set to AUTO instead.
- Is the air filter dirty? If so, replace it.
- Is the outdoor unit covered in dirt and debris? If so, clean it gently.
If you have taken these steps and the AC is still not cooling your house, contact Comfort First today. We offer affordable expert air conditioning repair services guaranteed to get your home feeling comfortable again.
Near Raeford NC, you can expect to pay between $3,500 – $6,000 for a new central air conditioner unit. This estimate includes installation costs, but will go up if new ductwork is needed. The final cost also depends on the quality of the unit you choose as well as the size of the unit you need in order to adequately cool your home.
Air conditioning units should be serviced once a year, preferably in early spring before it gets hot outside. Annual maintenance is very beneficial to your unit, in that:
- It has been proven to extend its lifespan so you won’t have to replace your AC anytime soon.
- It helps make the AC run more efficiently, saving you money on energy costs.
- It prevents future malfunctions and breakdowns from happening in the future.
for Raeford, NC
Our Reviews by City
Definitely would recommend them again if needed to anyone
Wynn - Raeford, NC
These two guys are keeper, didn't even know they were here.Did a marvelous job and mostly I'm warm, thank you
Great customer service !!
Tiffany - Raeford, NC
I’m so thankful for Comfort Air . The two gentleman we’re efficient . I had a great experience. My house is nice cozy . Thank you !!!!
Mr Billie - Raeford, NC
Rodney - Raeford, NC
Carmen - Raeford, NC
David reset the hard lockout and explained what to do if it should happen again. We appreciated his expertise.
Smith - Raeford, NC
Great job, very good experience
Darryl - Raeford, NC
Renee is a great professional sales representative
D. Rose - Raeford, NC
Very professional and knowledgeable. I’m very pleased with service that I received from Mr. Saucedo and his counterpart. I will recommend to others.
Germaine Jackson - Raeford, NC
Install crew was fast and informative, Thanks Comfort First
No hassle...Just honest pricing!
Del - Raeford, NC
I have enjoyed the costumer service I have received from with Bill Smith and Skyler Hunter. They both were very professional.
Working on a Goodman heat pump
Goodman heatpump package unit bad reversing valve
PAYNE package unit blown capacitor an contactor
Goodman hp frozen
Carrier hp.. Bad cfm
Goodman ac insufficient cooling
Trane equipment low charge
Carrier equipment insufficient cooling
Goodman equipment leak search
Goodman hp..low charge
Goodman ac insufficient cooling
Amana hp.replace txv
Amana no cooling
Complete 2 systems worked On DS Goodman Split heat pump: HO said the outside was making a weird noise. I found the system a little low in refrigerant but the valve system was leaking as soon as I took cap off. I added 1lb of r22 but did not charge customer due to us just doing maintenance and valve stem leaking. System is working great at this time.
Complete: 2 systems worked On DS Amana Split heat pump: We Installed. TN Said stopped working 2 days ago. I found the compressor not working. Found dead 45/5 cap. Replaced cap and system came on. Checked charge and working great at this time. Returning cap for warranty.
Goodman equipment blown capacitor
Trane equipment no cooling
Incomplete: 1System Payne Split HP: HO said it suddenly stopped working. I found zone board not sending signal to equipment. Straight wired to DS Tstat. Informed HO of findings and needs new zone board.
Complete: 1System Goodman Split heat pump: HO said would cool at night and not during the day. Found system 1lb low in r22.
Complete: 2 systems worked On DS unit. HO said was cooling properly. Found system low in refrigerant. Added 2lbs of 410a. SC 9° System working as it should at this time.
Goodman equipment sticking fan/ heatstrips
replaced ptrap on Goodman heat pump split unit AC zoned
added r22 refrigerant to Goodman heat pump split unit AC
performed diagnostic on carrier heat pump split unit AC zoned