We Put Your Heating & Air Conditioning Comfort First in Raleigh, NC
It’s in the name! When you work with Comfort First Heating & Cooling in Raleigh, NC for your heating and air conditioning repair service, your comfort really is our priority. Everything we do, including our heat pump services, whole home generator service, air conditioning services and furnace and heating services is centered around customer preferences.
Yes, Comfort First Heating & Cooling is an essential service provider during the COVID-19 virus outbreak. This is because Comfort First provides vital HVAC services that are essential for maintaining the safety, sanitation and operation of residences and businesses near Raleigh. HVAC contractors like Comfort First Heating & Cooling have unique skills that are important to public health and welfare.
Some things you can do to improve your indoor air quality in your Raleigh area home include:
- Keeping your house clean by regularly vacuuming, washing curtains and clearing clutter.
- Changing your air filters regularly.
- Letting fresh air in.
- Investing in an air purifier.
To learn more about indoor air quality and air purification systems, we are here to help. Comfort First specializes in the latest technology in indoor air quality and can help find the right solution for your home. Contact us today for better air tomorrow!
Replacing the heating and cooling system in your Raleigh home will cost on average between $6,800 – $12,300, including the replacement of ductwork. Around 80% of homes that need a new HVAC also need ductwork, but if yours does not, the price will be reduced by $2,000 – $3,000.
Average Cost: $9,500
Typical Range: $6,800 – $12,300
The AC in your Raleigh home that is running but not cooling may be experiencing one of the following problems:
- Thermostat is set to ON – When set to ON, the blower will continue to run, even when the system is not cooling your home. The unit should be set to AUTO to run properly.
- Dirty air filter – A dirty air filter can clog up the air circulation in your home. Replace your filters regularly to fix this issue.
- Dirty outdoor unit – When covered in dirt and debris, an AC cannot expel the warm air from your house. Clean units will function better and leave your house cooler.
- Tripped circuit breaker – Most ACs have an outside unit breaker and an inside unit breaker. Check to make sure that the outdoor breaker is not tripped, as the unit will continue to blow air into the house even though it is not cool.
Some problems will need to be addressed by a certified AC technician:
- Refrigerant Leak
- Leaking Ducts
- Faulty Compressor
If your AC is acting up, call the professionals at Comfort First today. We’ve been in business for over 20 years, providing excellent AC repair services to Raleigh and the surrounding areas. We guarantee courteous, dependable service with any job that we do. Contact us today for assistance with your air conditioner.
The average cost to have a whole house generator installed in the Raleigh area is between $500 – $3,000, not including the cost of the generator itself. The price is determined by the following factors:
- Site preparation.
- Connection to existing utility lines.
- New wiring and electrical panel upgrades.
- Permits and permissions.
- Materials and equipment.
At Comfort First, we provide full installation, service, and maintenance for whole home and standby generators. We offer many different types of generators to match your individual situation perfectly. Contact us today for a free estimate!
Your Air Conditioning and Heating Comfort is our Top Priority
See what your Raleigh area neighbors are saying about our service below or call us locally at (919) 985-7660 to schedule service.
for Raleigh, NC
Our Reviews by City
The Best Service Around!
Burnette - Raleigh, NC
We could not have asked for better service. Your technicians are extremely professional, courteous and considerate. They kept us informed every step of the way and we could not be happier with the new gaspak and ductwork. I give them five stars…. More if I could!
Great service on whole house generator
Wehner - Raleigh, NC
I was impressed with the 3 men who did our install! They worked extremely well together. They worked swiftly and well with each other.
Great Customer Service
Roger - Raleigh, NC
Service visit to correct a minor issue with the original inspection. Joshua did a great job to resolve the issue and even adjusted another issue not identified during the original inspection. Great customer service and more than willing to answer any questions.
Gavin - Raleigh, NC
Honesty goes a long way in the service industry, you can trust these guys.
Efficient and Professional Installation
Micha - Raleigh, NC
Sharpe - Raleigh, NC
He was well groomed, handsome, very polite and placed on shoe protectors upon entry of home. Explained everything and was quick to diagnose problem.
Great service. Super nice
Ashley - Raleigh, NC
Super nice. Came in, did what needed to be done and was out.
Great service! Very nice guys.
Shelby - Raleigh, NC
Gary - Raleigh, NC
Marie - Raleigh, NC
The technicians were professionals. Very Courteous!
Complete 2 Systems worked on DS Rheem Gas Furnace. EPA Heating Maintenance: cycled system. CHecked air filter. Checked blower motor amp draws. Performed a C0 check. Checked electrical wiring. Cleaned flame rod. Inspected heat exchanger. Tighten up screws. Inspected burners. System is running great at this time.
Complete 2 System EPA Heating Maintenace on both systems: DS Goodman Gas Pak: cycled system. CHecked air filter. Checked blower motor amp draws. Performed a C0 check. Checked electrical wiring. Cleaned flame rod. Inspected heat exchanger. Tighten up screws. Inspected burners. System is running great at this time. Us Carrier Gas Furnace: cycled system. CHecked air filter. Checked blower motor amp draws. Checked run Cap. Performed a C0 check. Checked electrical wiring. Cleaned flame rod. Inspected heat exchanger. Tighten up screws. Inspected burners. System is running great at this time. HO signed EPA agreement for DS system. She wants to pay with same payment type as for US.
Carrier gas furnace did maintenance
Lennox gas furnace replaced blower module and cycled system working at this time
Trane A/C checked system found water in secondary drain pan due to stopped up primmy drain line and cleared and cycled system working at this time
Lennox A/C replaced case coil amd recharge system with 7 lb R-22 and cycled system working at this time
Goodman A/C checked system and adjusted suoerheat and sup cooling and cycled system working at this time
Installed coil and ac outdoor
Installed gas furnace in attic and and coil. Also gaspack downstairs
Complete 2 Systems Worked on DS American Standard HP Split System. HO stated system was not coming on. Found bad dual cap. Used a 45/5 cap from truck stock. Checked pressures. System is running great at this time.
Complete 2 Systems worked on DS Rheem Straight A/C: HO stated tstat was not working. Found drain line stopped up. Float switch on secondary drain plug was cutting power to tstat due to drain line being stopped up. Replaced p trap and cleared drain line. Checked pressures. System is running great st this time.
Complete 2 Systems worked on DS Lennox Straight A/C: HO stated system was not working. Tstat not working properly. Found bad tstat. Couldnt change temp setting. Used a proselect non prog tstat from truck stock. Checked pressures. System is running great at this time.
Complete 2 Systems worked on DS Rheem HPSplit system. HO stated he heard a loud noise on the outdoor unit. Found bad run cap for cfm. Ised a 3 ud from truck stock. Checked cfm and compressor amp draws. Checked pressures. System is running great at this time.
Trane ac not cooling
Complete 1 System Gas Pak Straight A/C: HO stated system was not cooling. Found bad dual cap. Replaced it with a 35/5. Pressures are great.
Complete 2 Systems worked on US Trane Straight A/C: replaced blower motor and motor wheel. Replaced run cap. Used a 10 uf. From truck stock. Had to take a bunch of of things out of the way to get motor out and back in. Checked pressures. System is running great at this time.
Carrier low charge
Payne ac...low charge
Trane ac.low charge
Trane ac...not cooling
Complete 2 Systems worked on US Carrier 2 Zones Straight A/C: HO stated system was not cooling. Found bad dual cap. Used a 35/5 dual cap from truck stock. Pressures are great.
Estimate for new HVAC system
Trane equipment no ac
Carrier equipment leak search
Replaced drain pan...
Carrier ac replaced evap/coil
Added new package unit ,gas line, duct system
Complete 2 Systems worked on Us Carrier Straight A/C: HO stated system was not cooling. Found outdoor breaker tripped. Checked compressor windings. Checked dusl cap. Checked for burnt wires. Reset breaker. Found system 1 lbs low in R22. Added 1 lbs of R22. System is running great at this time.
Gibson split heatpump found unit 2lbs low on r22
Ruud gaspack preforme coil cleaning
Incomplete 1 System HP Split System: HO stated breaker was tripping. Found bad winding in compressor. Compressor needs to be replaced. Called arco to get part info. P#: AR22. Price:$278.48. In Stock. Called Leah, to check if we have any at the warehouse she stated we dont. System holds 8 lbs of R22. Ho said he just going for repaires.
Goodman A/C and case checked system found water in secondary drain pan due to stopped up primmy drain line and cleared and pumped water out of secondary pan and cycled system working at this time