For over 20 years, Rolesville, NC has known that Comfort First is the company to call for expert heating and cooling.
Our Rolesville, NC reviews show how we hold your heating, cooling and home comfort above all else! Come take a look!
for Rolesville, NC
Our Reviews by City
Dawn - Rolesville, NC
Great service, friendly staff!
Sal - Rolesville, NC
Satisfied with installation.
Complete 2 Systems Straight A/C: HO stated system was not cooling. Found System 2 lbs low in Ref. Added 2 lbs of 410A. System is running great at this time.
Complete 1 System 2 Zones Carrier Straight A/C: HO stated system was not cooling. Found drain pan full of water. Vacuumed out about 13 gallons of water. Found drain line stopped up. Drain outside was digged in the ground reason why it got stopped up. Had to dig ground to get drain line clear. Replaced p trap. Checked and made sure both motor dampers were working properly. Checked pressures. System is running great at this time.
Lennox ac...no issues
Carrier ac low charge
Carrier gas furnace preformed cooling maintenance
Complete. 1 system whole house. Carrier straight ac/gas furnace. 2010. Came to replace a txv. Performed quick re-diagnosis of system. Discovered dirty condenser coil and low on refrigerant. Cleaned coil and added 2lbs of r-410. Had a temp split of 20°. Cycled system. System is running at this time.
Lennox ac....low charge
Complete 1 system 3 presons Carier AC, perform EPA cooling maintenance. Checked thermostat and air filter. Checked blower motor amp draw. Checked all wiring. Checked run cap. Inpected evap coil. Made sure drain line was clear. Checked cfm and compressor amp draws. Checked all wiring at condenser. Checked dual run cap. Checked pressures. Cleaned condenser coil. System is running great at this time.
Nordyne duel fuel package unit. Repaired low voltage wire
Nordyne straight a.c. Replaced bad capacitor
Carrier split system Heat Pump
Carrie gaspack no issues
Goodman hp repair
Goodman hp check
Goodman Heat Pump
Carrier heat pump checked system found bad contactor and replaced and cycled system working at this time
Complete one system, downstairs system. Preformed heating maintenance and found no mechanical issues. System is operating properly at this time.
Carrier no ac leaking coil
Lennox replace zone control board