Trust Comfort First when it comes to your heating, air conditioning, indoor air quality and your full comfort picture for your home in Siler City, NC.
Thank you Comfort First Heating & Cooling
I just wanted to thank Joel and everyone who helped install our generator this week. Joel was super easy to work with and I really appreciate his timeliness and communication. Joel was great to explain the process from choosing a generator for our home, to ordering the generator and every step for installation. I especially appreciate his willingness to to offer solutions and options for our personal needs and situation. Everyone involved in our generator installation was professional and courteous. I am also thankful they left my home and their work area clean after each day of installation.
To see how we combine great customer service with professional heating and cooling services in Siler City, NC, check out our reviews below.
for Siler City, NC
Our Reviews by City
Bonilla - Siler City, NC
Great work ethic
Snaden - Siler City, NC
I love the way he explained everything so I would know what to expect, what was happening and why. Attention to detail was evident. When confronted with a problem, it was visible he was thinking in through and when he couldn’t, he didn’t try to BS his way out of it, he asked for help. That is honesty and transparency. Love it!
Dallas - Siler City, NC
Men worked quickly and effectively
Lennox hear pump checked system found CFM not running due to bad dual run capacitor and replaced and cycled system working at this time
Complete 1 System Amana Straight A/C: Checked thermostat and air filters. Checked blower motor amp draws. Checked all wiring. Inspected evap coil and blower wheel. Checked run cap. Made sure drain line was clear. Checked cfm and compressor amp draws. Checked dual cap. Found it way too weak. Talked to HO about it. She requested to get cap replaced. Replaced it with 35/5Uf. Used new one from truck stock. Old one was rusted out. Couldnt see size. Had to search it out.Cleaned condenser coil. Checked pressures. System is running great at this time.
Carrier gas pack need to pull blower motor and checked heat exchanger due to open roll out switch unable to due to due to rain
ICP heat pump checked system found bad defrost contral board need to replace contral board
Ruud package heat pump checked system found thermostat programed wrong and reprogrammed thermostat and cycled system working at this time
Complete 2 System worked on Main Unit Carrier HP Split System. HO stated system was not working properly. Found bad thermostat. Replaced it. Sysyem is running great at thi time
Carrier heat pump checked system found to be working at this time
Working on a Lennox package heat pump
Mini split no heat
Cimplete 1 System Amana HP Pak System performed Heating Maintenance. Checked all main components and wiring. Checked pressures. System is running great at this time.
Installed water coil air handler and ac outdoor unit
Goodman furnace no heat
Goodman furnace no heat pressure switch bad
Amana gaspack heating maintenance
Amana. Furnace heating maintenance
Complete one system. Found compressor and cfm not running due to bad dual capacitor and burnt wire going to capacitor. Replaced capacitor and repaired wire. System operating properly at this time.
Trane... blown 40/5 capacitor
Hail heat pump checked system found to be low in refrigerant and added 1 lb R-22 and cycled systems working at this time
Amanna heat pump completed coolong maintenance system and cycled systems working at this time
Ceckin duct work??
Amana split system
Amana hp....cooling tune up