Trust Comfort First when it comes to your heating, air conditioning, indoor air quality and your full comfort picture for your home in Siler City, NC.
Thank you Comfort First Heating & Cooling
I just wanted to thank Joel and everyone who helped install our generator this week. Joel was super easy to work with and I really appreciate his timeliness and communication. Joel was great to explain the process from choosing a generator for our home, to ordering the generator and every step for installation. I especially appreciate his willingness to to offer solutions and options for our personal needs and situation. Everyone involved in our generator installation was professional and courteous. I am also thankful they left my home and their work area clean after each day of installation.
To see how we combine great customer service with professional heating and cooling services in Siler City, NC, check out our reviews below.
for Siler City, NC
Our Reviews by City
Cary - Siler City, NC
Nate showed up within the time range, he was courteous, knowledgeable, and professional, but best of all - he fixed the problem quickly and checked that we were getting cold air before he packed up and left! We are very relieved and happy!
Bonilla - Siler City, NC
Great work ethic
Snaden - Siler City, NC
I love the way he explained everything so I would know what to expect, what was happening and why. Attention to detail was evident. When confronted with a problem, it was visible he was thinking in through and when he couldn’t, he didn’t try to BS his way out of it, he asked for help. That is honesty and transparency. Love it!
Dallas - Siler City, NC
Men worked quickly and effectively
Complete 2 Systems worked on Both. Heating Maint. BackSide Of House Bryant Gas Furnace with Rheem HP Split System(Duel Fuel System): cycled system. Checked tstat and air filter. Checked Blower Motor amp draw and run cap. Found run cap weak. Replaced it, uthorized by HO. Charger her Level 2 + tax. Used a 10 uf cap from truck stock. Checked electrical connections. No CO detected. Burners are clean. Cleaned Flame sensor. Checked amparage on draft motor. All safety switches are on great condition. HP Side, Checked colpressor and cfm amp draw, checked electrical wiring. Checked dual cap. Checked pressures. System is running great at this time. Front Side of House Amana 90% Gas Furnace: cycled system. Checked tstat and air filter. Checked Blower Motor amp draw. Checked electrical connections. No CO detected. Burners are clean. Flame sensor is clean. Checked amparage on draft motor. All safety switches are on great condition. System is running great at this time.
Complete 1 System Goodman Gas Pak EPA Heating Maintenance: cycled system. Checked tstat and air filter. Checked electrical connections. Inspected evap coil. No CO detected. Burners are clean. Cleaned Flame sensor. Checked amparage on draft motor and cap. All safety switches are on great condition. Checked draft motor. System is running great at this time.
Complete 1 System worked on a Carrier Straight A/C: Cooling Maintenance. Checked thermostat and air filters. Checked blower motor amp draw. Checked all wiring. Inpected evap coil. Made sure drain line was clear. Checked cfm and compressor amp draws. Cfm is over amping. Rated at 1.5 and amping 1.6. HO stated she will call. AHS and get dispatch transfered to us. Checked all wiring at condenser. Checked dual run cap. Checked pressures. Cleaned condenser coil. Other than cfm over amping System is running great at this time.
Trane Heat pump checked system found high head pressure and low suction pressure due to bad indoor TXV need to replace TXV
3 Trane heat pumps checked systems for high power bills found main floor system low in refrigerate amd week run capacitor for blower motor and completed repairs and cycled system working at this time
Goodman gas furnace found bad capacitor and contactor
Installed Briggs and Stratton 20KW whole home generator
Amanna heat pump completed cooling maintenance and cycled system working at this time
Trane heat pump and Amanna A/C and Amanna heat pump completed cooling maintenance and cycled system working at this time
Amana Heat Pump
Lennox hear pump checked system found CFM not running due to bad dual run capacitor and replaced and cycled system working at this time
Complete 1 System Amana Straight A/C: Checked thermostat and air filters. Checked blower motor amp draws. Checked all wiring. Inspected evap coil and blower wheel. Checked run cap. Made sure drain line was clear. Checked cfm and compressor amp draws. Checked dual cap. Found it way too weak. Talked to HO about it. She requested to get cap replaced. Replaced it with 35/5Uf. Used new one from truck stock. Old one was rusted out. Couldnt see size. Had to search it out.Cleaned condenser coil. Checked pressures. System is running great at this time.
Carrier gas pack need to pull blower motor and checked heat exchanger due to open roll out switch unable to due to due to rain
ICP heat pump checked system found bad defrost contral board need to replace contral board
Ruud package heat pump checked system found thermostat programed wrong and reprogrammed thermostat and cycled system working at this time
Complete 2 System worked on Main Unit Carrier HP Split System. HO stated system was not working properly. Found bad thermostat. Replaced it. Sysyem is running great at thi time
Carrier heat pump checked system found to be working at this time
Working on a Lennox package heat pump
Mini split no heat
Cimplete 1 System Amana HP Pak System performed Heating Maintenance. Checked all main components and wiring. Checked pressures. System is running great at this time.
Installed water coil air handler and ac outdoor unit
Goodman furnace no heat