Trust Comfrot First when it comes to heating, cooling and the full comfort picture in Southern Pines, NC.
To see how we combine great customer service with professional heating and cooling services in Southern Pines, NC, check out our reviews.
for Southern Pines, NC
Our Reviews by City
THE best AC company in the area, by far!!!
Theresa - Southern Pines, NC
This company was awesome from the very beginning! We work full time weekly careers & we were not the easiest client to schedule. I highly recommend Comfort Air of Sanford. We are grateful ‘
Dominic - Southern Pines, NC
Rennea is very professional and helped me twice now with getting a new unit
Complete: 2 System: EPA Maintenance:Upstairs Unit: Goodman Split Heat Pump: Air Handler: Checked Thermostat, Filters and Amp Draws on the Blower Motor, Inspected Evap coil. Checked condensate Pump. Heat Pump: Checked the charge, and the capacitor. Check the Amp draws on the fan and compressor. Cleaned Unit. Washed Coils System looks good and running Great at this time.
Goodman split heat pump. Replaced bad blower capacitor
Bryant split heat pump cooling maintenance
Goodman split heat pump. Replaced bad blower motor
Icp split heat pump. Cleared clogged drain line
2 system Trane split heat pump cooling maintenance
Goodman split heat pump. Cleared water from emergency pan, cleared drain line, and added 2 lbs of refrigerant
Goodman split heat pump. Replaced leaking evaporation coil and recharged system
Trane split heat pump. Repaired burned compressor wire
Repaired leak in trane heat pump
Replaced capacitor on Bryant heat pump
Replaced batteries in thermostat
Performed diagnostic on trane heat pump
Abed r22 refrigerant to Goodman heat pump
Helped homeowner select a new high-efficiency HVAC system to install next week.
Performed preventive maintenance on carrier heat pump.
Routine maintenance on a Goodman A/C
Working on a York Heat Pump
Carrie hp...no heat
Trane hp pack...not heating
Working on a lennox heat pump
Working on a carrier heat pump
Working on a goodman heat pump
Trane heatpump....compressor over heated as result of blown capacitor
Trane heatpump....breaker tripping