Trust Comfort First when it comes to heating, cooling and the full comfort picture in Spring Lake, NC.
To see how we combine great customer service with professional heating and cooling services in Spring Lake, NC, check out our reviews.
for Spring Lake, NC
Our Reviews by City
Tremendous installation reflecting there super knowledge and attention to detail. The crew was very courteous and helpful with all questions.
Helfgott - Spring Lake, NC
I will always recommend your company First and foremost to all our friends and family
Tommie - Spring Lake, NC
They were fast and efficient. They really knew their job
Katherine - Spring Lake, NC
Price - Spring Lake, NC
Royal - Spring Lake, NC
Bobby - Spring Lake, NC
Super nice, well informed and extremely helpful! Great guy
Mike - Spring Lake, NC
The technician (BJ) was very informative, very professional and knowledgeable
Rayon - Spring Lake, NC
Benjamin - Spring Lake, NC
We had to reschedule
Great AC service!
Jennifer - Spring Lake, NC
Michael went the extra mile to help get our AC back up and running. He was thorough in his service, checking the AC unit, air handler before ensuring the air vent output temperature was in the acceptable range.
Terrence - Spring Lake, NC
Great service, very polite
Stephanie - Spring Lake, NC
Leon - Spring Lake, NC
Great work professional
Ganesh - Spring Lake, NC
Found evap coil leaking on Goodman heat pump split
Replaced condesing coil on Goodman split heat pump
Complete 2 System Worked DS Goodman HP Split System Came to replace Compressor. Recover refrigerant, Removed Compressor, Repiped one of the lines. Set the new Compressor and brazed the lines. Cut out 2 filter dryers and Repiped one and added one filter dryer. Leak tested with nitrogen, pulled vacuum, added 6 lbs of 438A freon. Tested compressor. Got the right super heat and subcooling. Unit is running great at this time.
Working on a Ruud heat pump
Working on a Payne heat pump
Incomplete: 2 Systems: Worked on Both systems: The US system Goodman split HP: HO said wasn’t cooling. At the HP found system more than 3lbs low in refrigerant and needed to be leak searched. I explained to the HO about leak search procedure and she asked me to stop what I was doing and do not do leak search or anything due to the cost of r22. I explained to her that if we had to come back out she would have to pay another service fee to which she replied she wanted me to stop working on the system. So my diagnosis at this time is that the system is low on refrigerant and needs to be searched before can proceed. Complete DS Goodman HP split system HO said Unit was Not cooling. Turned on Thermostat, Unit outside didnt come on. Checked Capacitor. Replaced capacitor (30/5). Checked pressures. Unit is running great at this time. Used Truck Stock 30/5 Capacitor
Added 2lbs of r22 freon to rheem split heat pump
Payne package unit Heat pump cooling maintenance
Found bad CFM on Goodman package heat pump
Goodman split heat pump no cool
Trane split heat pump no cool
Replaced a thermostat and heat sequencers on a Payne package heat pump.
Installing a new Goodman split heat pump
Provided an estimate for a customer to replace their split heat pump. They decided to go with the 16 seer Amana.
Amana split heat pump cooling maintenance
Amana split heat pump maintance
Goodman heat pump found orange wire on condenser unit came undone rewired cycled system
Goodman heat pump found orange wire on condenser unit came on done rewired cycled system
2,5 tons gas package
Goodman split heat pump maintenance
Goodman and Heil split heat pump maintenance
2 tons Amana split heat pump
Goodman split heat pump no heat
4 unit Goodman split heat pump maintenance
EPA maintenance on a Goodman package unit