Trust Comfrot First when it comes to heating, cooling and the full comfort picture in Spring Lake, NC.
To see how we combine great customer service with professional heating and cooling services in Spring Lake, NC, check out our reviews.
for Spring Lake, NC
Our Reviews by City
Price - Spring Lake, NC
Royal - Spring Lake, NC
Bobby - Spring Lake, NC
Super nice, well informed and extremely helpful! Great guy
Mike - Spring Lake, NC
The technician (BJ) was very informative, very professional and knowledgeable
Rayon - Spring Lake, NC
Benjamin - Spring Lake, NC
We had to reschedule
Great AC service!
Jennifer - Spring Lake, NC
Michael went the extra mile to help get our AC back up and running. He was thorough in his service, checking the AC unit, air handler before ensuring the air vent output temperature was in the acceptable range.
Terrence - Spring Lake, NC
Great service, very polite
Stephanie - Spring Lake, NC
Leon - Spring Lake, NC
Great work professional
Ganesh - Spring Lake, NC
replaced thermostat on Payne heat pump AC split system
replaced blower motor and wheel on trane heat pump AC split system zoned
replaced blower motor on Goodman heat pump AC split system
cleared drain line on Goodman heat pump AC split system
replaced bypass damper on zone system
replaced compressor on Lennox heat pump AC split system zoned
Provided an estimate for a customer to replace their split heat pump. They decided on a 14 seer Amana with some minor duct modifications and a 10 year extended labor warranty.
Worked on Amana heat pump check system operation did not find any problem system running properly
Working on westing house
Provided an estimate for a customer to replace their split heat pump.
Arrived at customers house system is completely frozen solid need to return
Working on trane zone system
Working on goodman heat pumo
Working on intertherm airhandler
Complete: 1System: Nordyne split heat pump: Came to replace compressor cap and filter. Recovered 22 refrigerant removed compressor. Replaced Compressor Cap and filter dryer. Pressurized with nitrogen and pulled vacuum no leaks. Added 17 pounds of 438. Delta T 81-61 system looks good for running great at this time!
Complete: Amana Split HP: Came to replace AH Control Board. Removed old board. Drilled in new holes to mount control board higher bc it was sitting on wet duct at the bottom. Mounted new board. Turned system on checked Delta T. 81-61. System Looks good and running great at this time!
installed emergency drain pan for Goodman heat pump AC air handler
Perform 2 system annual preventive maintenance
Check two systems one unit completely Frozen other unit has bad condensing fan motor need to reschedule and repair
performed diagnostic on Goodman heat pump AC
Complete: Nordyne Split Heat Pump: Cane to change out zone board. Replaced old one rewired to fit Honeywell. Rewired downstairs Tstat to match board, cycled system and working great at this time.
Complete: Payne Split Heat Pump. Came to change blower motor. Switched it out checked charge and system is operating as it should at this time.
Complete: 2 Systems: Goodman Split Heat Pump: Worked on Upstairs Unit: HO said it continued to blow but stopped blowing cold air. At the HP found pressures off. Condenser coil stopped up. Cleaned coil, Checked charge. Charge was low. Added 1lb of refrigerant. Checked Amp draws and capacitor. Inside temp was 70° upstairs Delta T was 18. System looks good and working great at this time.
Incomplete: Ruud Split HP: Came to change out compressor. Checked compressor and it seemed to be running however the reversing valve would not switch over after adding power off and on. Before we replace the compressor we need to replace the reversing valve. Ordering part
InComplete: One system, Payne Split HP: HO said the AH sound led like the motor was going in and out. Outside found the HP running and line freezing up. Pulled disconnect. At the AH found blower motor just clicking and not running. Bad blower motor.