Trust Comfort First when it comes to heating, cooling and the full comfort picture in Summerfield, NC.
To see how we combine great customer service with professional heating and cooling services in Summerfield, NC, check out our reviews.
for Summerfield, NC
Our Reviews by City
Shawn - Summerfield, NC
Billy E was very professional and answered all of my questions. He was also in protective gear do to the COVID. Outstanding individual who represented not only Comfort First but himself as well. Great job Billy E I really appreciate your customer service.
Eileen - Summerfield, NC
Billy was very professional and took the time to explain everything to us. I put average for cost/pricing bc they need to come out to give me an estimate.
Billy is the man
Sam - Summerfield, NC
Billy is awesome. I loved his professionalism and he is the consummate professional. I am switching dromAHS to comfort because of billy! I only want him at my house...so comfort of you read this, I’m switching to you and please o my send billy to me house! Sincerely, Sam Davis Retired Marine and loving comfort!
Brice - Summerfield, NC
The HVAC Tech was very courteous and kind. Took time to explain all the different options and scenarios with our unit. He was prompt and on time. I appreciated that he had a discussion with us about our different options going forward and things to consider as our unit is a little older. He was very supportive and not pushy but just communicating good information. Overall great experience
great service. Prompt.
Charles - Summerfield, NC
Ronnie is a great tech. His knowledge and expertise is assuring.
Worked on Trane heat pump
Worked on Goodman air conditioner
Payne gas furnace replaced draft inducer and blower qheel and cycled system working at this time
Fujitsu mini spilt checked system found to be low in refrigerant and preferred leak search and found leaking evap coil need to replace evap coil
Work on Goodman heat pump
Work on Goodman heat pump
Worked on Carrier Air Conditioner
Goodman ac....no cooling
Comfortmaker replace gasvalve
Comfort maker diagnose bad smart valve part ordered
Comfortmaker....not heating.....smart valve
Carrier split heat pump replaced 2nd floor case coil recharge system
Carrier ac...replace evap/coil
Carrier ac...not cooling
2.5 gas furnace Amana
EPA maintenance on 2 Trane ac systems
Goodman airhandler....bad fan switch
Lennox Heat pump.
Goodman heat pump checked system found no power to air handler due to blown 60 amp fuse at service disconnect and tighten all electrical connections and replaced fuses and cycled system working at this time
Don’t work on York affinity systems
Checked system found to be a York Affinity system we dont work on this type of system