Trust Comfort First when it comes to heating, cooling and the full comfort picture in Wake Forest, NC.
To see how we combine great customer service with professional heating and air conditioning repair services in Wake Forest, NC, see what your neighbors are saying below.
for Wake Forest, NC
Our Reviews by City
Great service and honest/trustworthy approach!
Patrick - Wake Forest, NC
Carl came to my house within 3 hours of me contacting their office. Was very thoughtful putting shoe covers in before coming in asked a lot of questions before starting to get best idea of what was going on. Could have easily sold me on replacing as much as they wanted to but he gave me a basic run down of the situation asked what I thought and was made part of the process versus being told what to do. Carl was efficient with his time and had the issue resolved in less than 30 minutes. Now our HVAC unit is as good as new. Thank you Carl and the Comfort First Team!!!!
Mary - Wake Forest, NC
Kelli seems very personable and understands our current situation. It was a pleasure working with her.
Goodman heatpump package unit tune up
Goodman package unit tune up
Complete 2 System HPs Split Systems came to perform EPA maintenance US: Checked Air Filters and thermostat. Checked amp draws in blower motor, checked cap, inspected evap coil. Made sure drain line was clear. Checked all wiring. Checked amp draws in compressor and CFM, checked cap. Checked pressures. Cleaned condenser. Checked all wiring at condenser. System is running great at this time. Ds: Checked Air Filters and thermostat. Checked amp draws in blower motor, checked cap, inspected evap coil. Made sure drain line was clear. Checked all wiring. Checked amp draws in compressor and CFM, checked cap. Checked pressures. Cleaned condenser. Checked all wiring at condenser. System is running great at this
Goodman split heatpump preformed cooling maintenance
Carrier split heatpump preformed cooling maintenance
Carrier gas furnace preformed cooling maintenance
Goodman split system
Kenmore gas furnace and Trane ac checked system found to be working and maintaining temperature at the same
Lennox gas Furnace
EPA maintenance on 2 Goodman air conditioning systems
Goodman Gas Furnace
Lennoxe heat pump checked system found very dirty air filter and removed and cycled system working at this time
Replaced condensate pump
Goodman package heat pump bad blower motor
Carrier Heat Furnace
Goodman Heat Package Unit
Amana two stage gas furnace. Diagnosed bad low stage pressure switch