Trust Comfort First when it comes to heating, cooling and the full comfort picture in Wendell, NC.
To see how we combine great customer service with professional heating and cooling services in Wendell, NC, check out our reviews.
for Wendell, NC
Our Reviews by City
Great professional service
Carl - Wendell, NC
Had a new heat pump installed today and the service I received was great. These are a great group of guys. Top notch from start to finish. Thanks
Great job presenting new hvac system
Daniel - Wendell, NC
Very professional and very know
Cannon - Wendell, NC
Real customer service
Duane - Wendell, NC
I was able to talk over the problem with the service manager, the techs were very interactive and got the job done right and in a timely manner! A+!
Norydne heat pump checked system found grounded compressor
Ruud split heatpump preformed cooling maintenance
Amana split heatpump preformed cooling maintenance
Replaced thermostat on Carrier AC with gas furnace.
Carrier split heat pump. Replaced clogged filter drier and installed new outdoor piston
Complete 1 System Goodman Gas Furnace Syraight A/C System came to perform EPA Cooling Maintenance. Checked thermostat and air filter. Checked blower motor amp draw. Checked run cap. Found it out of its range. HO said he will wait until it goes bad. Checked all wiring. Inpected evap coil. Made sure drain line was clear. Checked cfm and compressor amp draws. Checked all wiring at condenser. Checked dual run cap. Found it out of its range. HO also said he will wait until goes bad. Checked pressures. Cleaned condenser coil. System is running great at this time.
Incomplete 2 System worked on US Carrier HP Split System. HO stated system was not heating or cooling properly in different occations. First thing I found was the yellow wire at condenser unit was not making full contact, the wires inside wire nut were connected right, wire nut was loose. Thats why when I was removing electrical panel cover I could hear contactor pulling in and out . Repaired wire. Also Found Piston for heating at the condenser stopped up. Piston and filter dryer will need to be replaced. Can use filter dryer from truck stock. Old Filter dryer is located Outside the AH unit. Talked to HO about the situation.
Replaced compressor and reversing valve on Goodman package unit.
Complete 1 System Amana HP Split System came to perform EPA Cooling Maintenance. Checked thermostat and air filter. Checked blower motor amp draw. Checked all wiring. Inpected evap coil. Made sure drain line was clear. Checked cfm and compressor amp draws. Checked all wiring at condenser. Checked dual run cap. Checked pressures. Cleaned condenser coil. System is running great at this time.
Carrier gas furnace checked system found bad contral board need to replace contral board
Goodman air handle replaced zone damper motor and zone contral board and cycled system working at this time
Carrier heat pump checked system found defrost sencer not properly mounted and repired and cycled system working at this time
Goodman gas pack repaired dented duct shroud
Amana split heat pump 3 zone. Reprogrammed thermostat after power outage
Carrier gas package unit. Replaced heat exchanger and flue cover
Goodman split heat pump Added refrigerant
Goodman split heat pump. Diagnosed leaking evaporator coil
Goodman split heat pump 3 zone. Diagnosed bad zone damper motor and control board
Goodman split heatpump found bad zone board and zone damper
Goodman hp no heat...no power on home
Complete 2 System worked on DS Tempsar dual fuel system came to replace compressor. Replaced old compressor added refrigerant. Checked pressures system is running great at this time.
Ruud split heatpump changed thermostat
3.5 ton heat pump change out. Goodman 14 seer
Complete: 1System EPA Maintenance: Trane Str8 AC GAS Furnace: US Furnace: Checked the Amp Draws on the blower motor. Checked the capacitor. Checked Heat Exchanger. Cleaned burners, Flame sensor and Checked Roll out switch. Cleaned it out. System looks good and working good at this time.